<?xml version="1.0" encoding="UTF-8" standalone="no"?><image-reference id="_c6b33835-c6c9-4ba2-b79c-70210284bed8"><num>9.5.3</num><title id="_52a9fd24-298f-4cea-8415-a869a00fb3b8">Class 1b building where multiple bedrooms are served by a hallway</title><image alt="Class 1b building where multiple bedrooms are served by a hallway" height="468" heightdpi="200" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/9-5-3-class-1b-building-where-multiple-bedrooms-are-served-by-a-hallway.svg" width="1200" widthdpi="200"><image height="468" heightdpi="200" href="C:\Users\bkiem\AppData\Roaming\Quark\XML Author\Temp\media1_8e3dc2fb-3e6b-48b7-a39e-5b7d04c65d65.jpg" width="1200" widthdpi="200"/></image><desc-note id="_b706870f-5083-405c-93b8-bbf8b36e1ff0"><ol outputclass="numbered"><li id="_c9b4d9ac-fda3-4f46-818a-8f601568a7c3">In this diagram—<ol><li id="_e0e94dab-cb29-460d-812a-2c6823d22005">the location of each smoke alarm is indicated by a black dot; and</li><li>the location of a smoke alarm with evacuation lighting is indicated by a black dot within a square; and</li><li>the area served by evacuation lighting is indicated by grey shading.</li></ol></li><li id="_4695d675-3608-4508-9114-9b1f95f20374">Smoke alarms are <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_2c4cdbdd-4bfb-41d1-b5e0-59c1cfda73cc" inv:access="external" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">required</xref> to be interconnected by <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1956_1.1.0.xml#_eb1fc6ca-5706-44ff-9a2d-26b6a683430a" id="_c3bbcc7c-8052-47ec-a660-7cdfc4bbf52a" inv:access="external" referencetype="Text" scope="local" synctargettext="false" type="subclause">9.4.1(d)</xref>.</li><li id="_e8df2f96-35db-4678-8414-d76f476b3802">Lighting in the grey shaded area is to be activated by a smoke alarm if using <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1962_1.2.0.xml#_e0e89afb-9b94-4dd3-ab6d-f5803eedf0f2" id="_6cbc1a28-bca7-409a-870c-284b35722e78" inv:access="external" referencetype="Text" scope="local" synctargettext="false" type="subclause">9.5.5(b)(ii)</xref>.</li></ol></desc-note></image-reference>