<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_5189c05f-c243-44c0-91f8-ed1def11091a" outputclass="ncc-clause" variation="NSW"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D46</sptc><title id="_84a6ddf9-f24e-4173-a886-e2783a7ef8d3">Projection suites: rooms to be provided</title><archive-num>2019: NSW H101.17.1</archive-num><subclause id="_8c181101-ca52-42a5-b6df-0ddb45c13593" outputclass="subclause"><title id="_225fd2ce-5577-419b-b11b-b95f8bb7cf56">SubClause</title><num>1</num><p>A <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2457_4.0.0.xml#_9c468f5f-cc5c-46d4-bd24-18206a0a6881" id="_0059e7fd-6fcf-491e-ae55-bbdc5bf2832f" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">projection suite</xref> in accordance with the staffing requirements of Schedule 72 of the Environmental Planning and Assessment Regulation 2021 must contain either—</p><ol outputclass="alpha"><li id="_4e805a62-1107-46a9-a937-7f995571a5f3">a projection room and sanitary accommodation comprising at least 1 closet pan and 1 washbasin, where the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2457_4.0.0.xml#_9c468f5f-cc5c-46d4-bd24-18206a0a6881" id="_ad1198ae-b69c-42c4-865a-67ec4dd9609b" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">projection suite</xref> is continually staffed; or</li><li id="_8bde38fe-02ca-4c50-8717-c9a7ced05ac1">a projection room fitted with the following equipment—<ol><li id="_aff68016-4309-498d-a354-976f76d73f3d">an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_d739de56-6c95-4eae-bec7-5d900768bad1" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">automatic</xref> fire suppression system in accordance with SSL Appraisal Specification FAS 102 or a sprinkler system complying with AS 2118; and</li><li>a smoke detection system which will—<ol><li>comply with AS 1670.1; and</li><li>be connected to a fire station or other approved monitoring service where arrangements are in place to initiate <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1275_0.4.0.xml#_cc69b717-0915-4071-87d9-176353f8cc9a" id="_9186c473-f54e-493d-94e1-12cd0df787e3" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">fire brigade</xref> response; and</li><li>close down all shutters fitted to projection or observation ports; and</li><li>activate sufficient general lighting to provide a minimum of 40 lux measured at floor level in any <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2329_1.0.0.xml#_29badeb5-89c1-45af-a10d-fb25847d52c3" id="_12a8c98a-e0bd-4246-ad69-1931bd7f33ed" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">auditorium</xref> affected; and</li><li>operate a public address system to automatically announce a suitable message from the management of the premises; and</li><li>activate an audible alarm to immediately indicate to management the presence of smoke in the projection room.</li></ol></li></ol></li></ol></subclause></clause>