<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_59313f49-8661-47a8-bf4a-86708a3c257b" outputclass="ncc-clause" variation="NSW"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D8</sptc><title id="_24260d77-281c-44ba-af46-2a38857f15df">Conventional stages: large stages</title><archive-num>2019: NSW H101.5.3</archive-num><subclause id="_ca44b4a1-ed79-48c9-b8dd-3a0ead2076f6" outputclass="subclause"><title id="_4162b7ae-a5be-4468-b4ba-5cdc67d617ce">SubClause</title><num>1</num><p>A <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_6fc53628-eac9-4df4-97d6-47384125a20d" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stage</xref> which is more than 150 m<sup id="_cbeec083-931f-43ec-8faa-74f7bbc454ea">2</sup> in area—</p><ol outputclass="alpha"><li id="_b86ce7dd-aed5-43be-baa8-4237446c09b0">must have installed directly above the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_687668ca-ca59-480a-afc4-e48099712702" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stage</xref> a suitable sprinkler system (other than a FPAA101D or FPAA101H system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_a2923a4b-928d-440f-a527-0c3caf3b0627" referencetype="Text" scope="local" synctargettext="false" type="specification">Specification 17</xref>; and</li><li id="_cc442be1-3cda-4a4c-8fc6-86bff01e80ed">must have the proscenium opening protected by a safety curtain that complies with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6723_0.5.0.xml#_baee8254-c03b-43b4-aa0c-d117148f0b49" id="_9a303cf6-a207-4f07-b86f-70806d368e97" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">NSW I4D15</xref> and <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6724_0.4.0.xml#_abae7c34-c6be-4054-b3fc-2f1859b29285" id="_5ed3b12c-544d-43ff-9e92-f30278d1e80a" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">NSW I4D16</xref>; and</li><li id="_9229714b-3e49-478f-9054-bd99f7249f73">must have a line of open drenchers or open sprinklers provided above the proscenium opening on the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_257560d9-888f-43a4-a068-8befd40e256f" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stage</xref> side and in such a position as to be able to discharge over the inside face of the safety curtain; and</li><li id="_e02c348f-9229-4f59-90d4-55b26535a941">must have 2 or more means of egress from the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_b5a2365a-7a2f-4458-9052-c6602819fa52" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stage</xref> and <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1207_1.0.0.xml#_a664353a-ef5b-4cd2-b68b-f2db1db81dce" id="_bc3122f1-5886-4ddb-a9f1-74d93b7a48de" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">backstage</xref> area provided otherwise than through the proscenium wall.</li></ol></subclause></clause>