<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_6a76df06-3a43-43e4-9681-d7470504ee63" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>G1D3</sptc><title id="_8bb625d9-397c-401b-a144-60a5b1cb25b7">Refrigerated chambers, strong-rooms and vaults</title><archive-num>2019: G1.2</archive-num><subclause id="_b8aeb86b-2ed5-4960-bcdf-4bd65c964233" outputclass="subclause"><title id="_1018f91d-b49f-458c-9e49-bf424423fb87">SubClause</title><num>1</num><p>A refrigerated or cooling chamber, strongroom or vault that is of sufficient size for a person to enter must have—</p><ol outputclass="alpha"><li id="_109af731-89ec-410d-9cf6-cf9c2a35df6f">a door which is capable of being opened by hand from inside without a key; and</li><li id="_967e5492-1a4f-4081-a685-c96d104cded7">internal lighting controlled only by a switch which is located adjacent to the entrance doorway inside the chamber, strongroom or vault; and</li><li id="_51d679ff-865c-4116-bd1d-92b0cd4e7e2b">an indicator lamp positioned outside the chamber, strongroom or vault which is illuminated when the interior lights <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_0e55ab01-2271-4ece-bfec-d335e319db22" scope="local" type="abcb-glossentry">required</xref> by (b) are switched on; and</li><li id="_aa871175-2a24-4f97-b350-fd28934a0828">an alarm that is—<ol><li>located outside but controllable only from within the chamber, strongroom or vault; and</li><li>able to achieve a sound pressure level outside the chamber, strongroom or vault of 90 dB(A) when measured 3 m from the sounding device.</li></ol></li></ol></subclause><subclause id="_5a6c002a-0806-4235-859e-9e60e6263070" outputclass="subclause"><title id="_372c4327-429d-491f-9044-2384a8fb994f">SubClause</title><num>2</num><p>A door <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_85e844ce-707b-490d-a6af-717ecd6494ce" scope="local" type="abcb-glossentry">required</xref> by (1)(a) in a refrigerated or cooling chamber must have a doorway with a clear width of not less than 600 mm and a clear height not less than 1.5 m.</p></subclause></clause>