<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_e5731ac1-154e-454e-81c1-7d962572d39f" outputclass="ncc-clause" variation="VIC"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S20C8</sptc><title id="_e620be41-e072-44ff-a7b6-e006ced61bc1">System monitoring</title><archive-num>2019: VIC Spec E2.2a: 8</archive-num><subclause id="_8369bd8a-d427-4793-8652-12d2e6fb2d58" outputclass="subclause"><title id="_a46e6669-56eb-46d9-85ed-d042ea6223cd">SubClause</title><num>1</num><p>The following installations must be connected to a fire alarm monitoring system connected to a fire station or a fire station dispatch centre in accordance with AS 1670.3:</p><ol outputclass="alpha"><li id="_dc70dde1-f426-4c8d-9799-29ad294a7158">A smoke detection system in a Class 3 building provided in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_4fb9883e-9f7d-458e-8f3c-86c68910ed3e" id="_0fd8609c-ecb2-4e01-a243-42e674e712e4" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">S20C2(b)(i)</xref> or <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_4fb9883e-9f7d-458e-8f3c-86c68910ed3e" id="_a37f9549-1450-4a5b-a14a-dcbce28a29f6" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">(ii)</xref>.</li><li id="_2f4fea58-aaae-4ae2-9325-354ea3a80c68">A smoke detection system in a Class 9a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1333_0.4.0.xml#_1f5fbee8-584a-4244-9286-ebf9d8ebb04a" id="_40df944a-8e25-4429-b74b-e3ba78e3fba8" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">health-care building</xref>, if the building accommodates more than 20 patients, unless the building is sprinklered and the sprinkler system is permanently connected to a fire station, or other approved monitoring service with a direct data link to a fire station, in accordance with Building Practice Note FS-01.</li><li id="_d56e768c-3d18-44de-ba9d-ae9b73db8ce8">Smoke detection in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/672_7.5.0.xml#_38696b94-36c5-42a0-a851-78ecd6b31308" id="_57fb4fbb-342c-46a9-a72a-26add9bd889b" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">S20C6</xref> provided to activate—<ol><li id="_62284b81-d4dd-429a-9443-bfd407dd1a12">a smoke exhaust system in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/178_0.3.0.xml#_6d2c51ee-0d29-462a-a5c4-36126343e0bb" id="_26d34182-260a-4072-9658-13b6e7227dcb" referencetype="Text" scope="local" synctargettext="false" type="specification">Specification 21</xref>; or</li><li><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1467_0.4.0.xml#_425cb075-105b-486b-834a-75d429b02edc" id="_98611ed1-eeb5-40d2-a006-bc3c78aec711" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">smoke-and-heat vents</xref> in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/180_0.3.0.xml#_786dafbe-bc7c-47bb-9057-7afae7a7da08" id="_1a2cbce5-86c8-4522-99af-eec4d46c3c2d" referencetype="Text" scope="local" synctargettext="false" type="specification">Specification 22</xref>.</li></ol></li><li id="_711c4e16-aca4-427d-a020-11c93b9c6e9c">An <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_7ecf7b9b-b039-4900-a33b-496f5d290570" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">automatic</xref> fire detection and alarm system <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_16de5d48-5d6f-4774-8078-926b1b064b7f" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">required</xref> by <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2703_1.9.0.xml#_b7abbb05-33f2-434d-a550-8f0b3d2c865e" id="_b9ec6442-dea5-4e3f-bf10-5af177b61581" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">E2D10</xref> for large isolated buildings subject to <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1152_1.7.0.xml#_6ed8026f-71b8-4618-a419-79b7053b0c98" id="_6e7e08df-70dc-4444-8e08-cdaec3386813" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">C3D4</xref>.</li></ol></subclause></clause>