<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_d99e1c36-e70b-4d40-bb3d-a2a4c7c68359" orientation="Portrait" variation="SA"><num>E1D2</num><title id="_1417783e-82d6-45d1-80f2-057bbe4828b8">Minimum quantities for on-site water supplies for farm buildings</title><table id="_5c8d90ea-a879-4e77-8225-5a742f529c6a" keycol="1"><tgroup cols="3"><colspec colname="001" colnum="1" colwidth="144.05*"/><colspec colname="002" colnum="2" colwidth="143.95*"/><colspec colname="003" colnum="3" colwidth="144.05*"/><thead><row><entry>Building Group</entry><entry><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1314_2.10.0.xml#_7da927fe-453e-424f-b6ec-280f4e464397" id="_aadb20c1-b1a0-4329-a40b-a1a30356d31c" scope="local" type="abcb-glossentry">Floor area</xref> (m<sup id="_a0055d13-c1f6-41f7-8c28-07be8b4316a9">2</sup>)</entry><entry>Minimum water supply quantity (L)</entry></row></thead><tbody><row><entry morerows="2">Group A</entry><entry>500 to 1,000</entry><entry>36,000</entry></row><row><entry>1,001 to 2,000</entry><entry>72,000</entry></row><row><entry>2,001 to 5,000</entry><entry>144,000</entry></row><row><entry morerows="1">Group B</entry><entry>500 to 1,000</entry><entry>72,000</entry></row><row><entry>1,001 to 2,000</entry><entry>144,000</entry></row><row><entry>Group C</entry><entry nameend="003" namest="002">5 L/m<sup id="_dfaefb48-7d6f-45d4-8cb1-605b48044577">2</sup> or 36,000 L at each location, whichever is greater</entry></row></tbody></tgroup></table><desc-note id="_1ebbcf2e-0d67-4fc9-bd1a-ee18a3c9e286"><p>A single water supply with the minimum water quantity outlined in Table SA E1D2 can serve more than one building.</p></desc-note></table-reference>