<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_eaa82025-9228-4e39-a607-588f128b0511" outputclass="ncc-clause"><sptc>S2C19</sptc><title id="_15d04c23-1ef4-4da5-b8e7-601f6faeb220">Exposure of columns</title><archive-num>2019: Sch. 5 (Annex): 8.1</archive-num><subclause id="_e53401d3-ac4c-44b8-a251-e3bfda139cb1" outputclass="subclause"><title id="_ebfeadfb-d431-43e7-adcc-21c9ae419a6e">SubClause</title><num>1</num><p>A column incorporated in or in contact on one or more sides with a wall of solid masonry or concrete at least 100 mm thick may be considered to be exposed to fire on no more than 3 sides.</p></subclause></clause>