<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_ed833c33-057f-4090-b31e-0922b936f15d" outputclass="ncc-clause" variation="NSW"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S20C8</sptc><title id="_71c908ff-71e6-483f-b59d-6307aba9e096">System monitoring</title><archive-num>2019: NSW Spec E2.2a: 8</archive-num><subclause id="_63813cab-7fc7-4188-8b59-d7fbd0f6a411" outputclass="subclause"><title id="_2a972b80-67d3-4dc6-a4a9-4a8f4dc010f5">SubClause</title><num>1</num><p>The following installations must be connected to a fire alarm monitoring system connected to a fire station or fire station dispatch centre in accordance with AS 1670.3:</p><ol outputclass="alpha"><li id="_5f966d12-2a03-4611-9339-fc6da662cfed">A smoke detection system in a Class 3 building provided in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_4fb9883e-9f7d-458e-8f3c-86c68910ed3e" id="_feadb2cb-f53a-42c8-8796-1c3513accb99" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">S20C2(b)(i)</xref> or <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_dbd37359-2581-4e5f-aa46-179171e12856" id="_5ef8cddd-cb71-4e95-8095-5188d475fd05" referencetype="Text" scope="local" synctargettext="false" type="subclause">S20C2(b)(ii)</xref>.</li><li id="_e15ef8f4-ac8f-467e-983a-6dfb710fcb81">A smoke detection system in a Class 9a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1333_0.4.0.xml#_1f5fbee8-584a-4244-9286-ebf9d8ebb04a" id="_4c6fcba4-4646-469b-b97b-1cd1a34069c8" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">health-care building</xref>, if the building accommodates more than 20 patients.</li><li id="_bef5f819-744a-42a4-8469-2008b9072620">A smoke detection system in a Class 9c building.</li><li id="_903db2ad-3b33-4478-891e-e0fc0120d490">Smoke detection in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/672_7.5.0.xml#_38696b94-36c5-42a0-a851-78ecd6b31308" id="_5d3dcafa-53aa-436a-aae0-28cbb0f02bbc" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">S20C6</xref> provided to activate—<ol><li id="_d46ac99a-a77b-4d4d-847f-1776db9b40de">a smoke exhaust system in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/178_0.3.0.xml#_6d2c51ee-0d29-462a-a5c4-36126343e0bb" id="_76de7fc6-211b-48d0-a7a9-979d54baab2e" referencetype="Text" scope="local" synctargettext="false" type="specification">Specification 21</xref>; or</li><li><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1467_0.4.0.xml#_425cb075-105b-486b-834a-75d429b02edc" id="_14e95578-73e4-423f-90cc-0d8de04d4805" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">smoke-and-heat vents</xref> in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/180_0.3.0.xml#_786dafbe-bc7c-47bb-9057-7afae7a7da08" id="_d668bb24-9eca-4d49-a647-fe4390c7d452" referencetype="Text" scope="local" synctargettext="false" type="specification">Specification 22</xref>.</li></ol></li></ol></subclause></clause>