<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_2d9827ae-bc84-4cff-a2e5-9afd6fe97a6b" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S31C9</sptc><title id="_b20dd092-fa66-441d-9bdb-8abffe90419c">Activation of smoke control system</title><archive-num>2019: Spec G3.8: 3.3</archive-num><subclause id="_2afb9136-7299-4360-b9ec-da2e0b8bd516" outputclass="subclause"><title id="_5a34cc18-fe71-4fb9-bf0c-d9e62c1f1e81">SubClause</title><num>1</num><p>The smoke control system must be activated by—</p><ol outputclass="alpha"><li id="_c6b68571-a8fc-4826-a64c-de6db64e9274">operation of an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_d67afcb4-c7cc-4fd1-81bd-1b0d09955bec" scope="local" type="abcb-glossentry">automatic</xref> fire alarm; or</li><li id="_3d493458-be16-49a9-b198-1c1520c26f53">operation of the sprinkler system; or</li><li id="_55e96081-a965-4988-a2a4-7b1256095a3a">a manual start switch.</li></ol></subclause><subclause id="_71077a29-9b26-4518-ad99-ecdee8850d6f" outputclass="subclause"><title id="_6b1c29a4-c676-4b2f-acc3-484a40b56f7f">SubClause</title><num>2</num><p>All controls for the smoke control system must be located—</p><ol outputclass="alpha"><li id="_c66e9c62-9233-4396-98c6-4b4751bfd809">in the fire control room; or</li><li id="_054ad032-0356-495d-90d0-972d28d699f1">in the emergency control centre (if any); or</li><li id="_d420a99b-933e-40ea-b084-a8cacb1f3a51">adjacent to the sprinkler control valves; or</li><li id="_1cc330fb-2409-4953-a750-c596078db00e">incorporated in the Fire Indicator Panel.</li></ol></subclause></clause>