<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause"?><clause id="_2f639ea1-0c6f-40be-975e-c9586da4797e" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>J7D5</sptc><title id="_0f328a39-6baa-427a-a6d4-941b6142e621">Interior decorative and display lighting</title><archive-num>2019: J6.4</archive-num><subclause id="_edd7fef0-14ec-4d02-9c54-28a4e5dc9edf" outputclass="subclause"><title id="_5130d2aa-b0a0-44e1-8e2f-6a0cf33285d3">SubClause</title><num>1</num><p>Interior decorative and display lighting, such as for a foyer mural or art display, must be controlled—</p><ol outputclass="alpha"><li id="_0bc1c035-2076-47a3-a618-7a1f76bcc885">separately from other artificial lighting; and</li><li id="_542fb3a5-6eaf-43b0-8eb1-d281f30a6e31">by a manual switch for each area other than when the operating times of the displays are the same in a number of areas such as in a museum, art gallery or the like, in which case they may be combined; and</li><li id="_aa295be5-fa3f-41c8-a209-485e17aef343">by a time switch in accordance with <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/216_0.4.0.xml#_ba73ea46-882f-40c3-9a4a-3286316be594" id="_ff38779a-beb8-4896-9752-e298674e846f" inv:access="external" scope="local" type="specification">Specification 40</xref> where the display lighting exceeds 1 kW.</li></ol></subclause><subclause id="_6adf4b08-879d-47dc-86cd-3eb1ee9198c6" outputclass="subclause"><title id="_9c37051d-14f4-43d8-9df3-e56661af16a0">SubClause</title><num>2</num><p>Window display lighting must be controlled separately from other display lighting.</p></subclause></clause>