<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_c8d37f45-1f82-4641-a1f0-01c4c63fe1c5" outputclass="ncc-clause"><sptc>B1P5</sptc><title id="_e9d74373-5256-4e84-86e4-814480f0aff3">Pressure</title><archive-num>2019:BP1.2, TAS Exemption 1</archive-num><subclause id="_efb150f4-c41b-4db2-8222-3cadb7957a65" outputclass="subclause"><title id="_32d93519-4072-481d-a9ae-359bc2762640">SubClause</title><num>1</num><p>The points of discharge for a cold water service must—</p><ol outputclass="alpha"><li id="_cd340415-fe69-42d1-a5f6-edec02cbe777">have—<ol><li>a working pressure of not less than 50 kPa; and</li><li>a static pressure within the building of not more than 500 kPa; or</li></ol></li><li id="_3bdf5596-ceec-41b4-9904-ab209541e92a">have water pressures suitable for the correct functioning of the fixture or appliance where water pressures outside of (a)(i) and (a)(ii) are required. </li></ol></subclause><callout id="_892d5bf3-47f9-41ac-8aae-37a4c2f28325"><callout-type ncc-info-type="exemption"/><p>B1P5(a)(i) and B1P5(a)(ii) do not apply to existing low-pressure gravity only water services.</p></callout></clause>