<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_8d03e2c3-97a5-4ffa-ba82-94e22898d0db" outputclass="ncc-clause" variation="WA"><sptc><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:39:00" xt:id="7ad71166-3c9c-47f3-adcf-62406fa94a88"/>C1D3<xt:insText xt:action="end" xt:id="7ad71166-3c9c-47f3-adcf-62406fa94a88"/></sptc><title id="_ac32e479-11c5-49b7-a1d4-92270c275526"><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:39:00" xt:id="510c0c7a-b452-48b2-9cbd-704d4ba209ed"/>General requirements<xt:insText xt:action="end" xt:id="510c0c7a-b452-48b2-9cbd-704d4ba209ed"/></title><archive-num><placeholder outputclass="placeholder">[ARCHIVE]</placeholder></archive-num><subclause id="_f608f87d-1ea8-4a7b-bf0c-5a51510f336c" outputclass="subclause"><title id="_a75f5827-f6ca-4292-8197-13b15baef094">SubClause</title><num><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:40:00" xt:id="e8df81bf-ccbd-4c37-8024-780b36725a44"/>1<xt:insText xt:action="end" xt:id="e8df81bf-ccbd-4c37-8024-780b36725a44"/></num><p><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:40:00" xt:id="64cb1bb9-608d-47f8-b7c8-2b6056246f23"/>A sanitary plumbing system must be in accordance with AS/NZS 3500.2 with the following variation:<xt:insText xt:action="end" xt:id="64cb1bb9-608d-47f8-b7c8-2b6056246f23"/></p><ol outputclass="alpha" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:43:12" xt:type="insert"><li id="_0a9bd303-5d8c-4ced-a98c-efc124651c2a" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:43:12" xt:type="insert"><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:43:00" xt:id="4b290639-2feb-411b-b5b7-b90279af81b8"/>Bends in pipes shall —<xt:insText xt:action="end" xt:id="4b290639-2feb-411b-b5b7-b90279af81b8"/><ol xt:author="Lee Liu" xt:dateTime="2025-01-07T09:43:59" xt:type="insert"><li xt:author="Lee Liu" xt:dateTime="2025-01-07T09:43:59" xt:type="insert"><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:44:00" xt:id="a0594e03-39d5-4a49-be72-558a245c30a5"/>have a throat radius complying with AS/NZS 1260:2017 (PVC-U pipes and fittings for drain, waste and vent applications) Table 5.6 and Figure B6; and<xt:insText xt:action="end" xt:id="a0594e03-39d5-4a49-be72-558a245c30a5"/></li><li xt:author="Lee Liu" xt:dateTime="2025-01-07T09:44:01" xt:type="insert"><xt:insText xt:action="start" xt:author="Lee Liu" xt:dateTime="2025-01-07T09:44:00" xt:id="c6cbedbb-6318-432d-b52e-58a1c54919e4"/>be free from wrinkling and flattening<xt:insText xt:action="end" xt:id="c6cbedbb-6318-432d-b52e-58a1c54919e4"/></li></ol></li></ol></subclause></clause>