<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_b3224267-f1e5-49a2-9dd5-e859ca990765" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>E1D15</sptc><title id="_f52d71da-588e-43cb-9d98-0f02b1aa88d3">Fire control centres</title><archive-num>2019: E1.8</archive-num><subclause id="_b00bb841-e674-4b60-bf29-205ae5a90a00" outputclass="subclause"><title id="_7583a2c1-afef-4e13-9e53-2a665aec25e5">SubClause</title><num>1</num><p>A fire control centre facility in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/172_0.3.0.xml#_8106698a-700d-4642-b09c-e17d1cf482be" id="_48ac7759-c058-45ee-9dad-28cc2c2a8f2d" scope="local" type="specification">Specification 19</xref> must be provided for—</p><ol outputclass="alpha"><li id="_9a41220f-c738-4f06-9ea3-5ce6a2878769">a building with an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1252_2.0.0.xml#_cd986c21-bc64-43a9-954d-86e35d335b74" id="_4a7cba17-92b8-41fa-80e0-70ec07f89a92" scope="local" type="abcb-glossentry">effective height</xref> of more than 25 m; and</li><li id="_33b194b0-9111-4fb8-9cb5-16cbc9b0b49f">a Class 6, 7, 8 or 9 building with a total <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1314_2.10.0.xml#_7da927fe-453e-424f-b6ec-280f4e464397" id="_82e55fec-0c8d-4ce4-8c08-039bea02450b" scope="local" type="abcb-glossentry">floor area</xref> of more than 18 000 m<sup id="_f135375e-f21f-43b6-bc6a-6c5a2f2c5919">2</sup>.</li></ol></subclause></clause>