<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_becc56ea-598d-44bd-97d3-29a3ac465d3c" outputclass="ncc-clause" variation="NSW"><sptc>B2D5</sptc><title id="_77d0128c-a3ec-42e4-991c-3c1d5663c10c">Maximum delivery temperature</title><archive-num>2019: NSW B2.5(a)(iv)</archive-num><subclause id="_3651ce26-b6ad-4987-b146-20f9a11b59c4" outputclass="subclause"><title id="_013c5719-3547-46c5-a2fa-d95e3cc8901e">SubClause</title><num>1</num><p>The delivery temperature of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1334_0.4.0.xml#_92b3a3dc-59e4-425f-909b-d8eb03e6460a" id="_85bd9201-562e-4b8e-9e95-51521c9649d1" scope="local" type="abcb-glossentry">heated water</xref> at the outlet of each sanitary fixture must be—</p><ol outputclass="alpha"><li id="_ebf05f85-02fe-4d45-bb51-d6ce1458d67a">not more than 45°C in any—<ol><li>residential part of an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1180_1.0.0.xml#_41ac03c9-62e4-45df-84a3-8f31abb6b147" id="_6df732f2-2c21-4087-9070-2b8b76943ddc" scope="local" type="abcb-glossentry">aged care building</xref>; or</li><li><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1393_4.0.0.xml#_63b56568-e9c9-425f-8456-a332503c9520" id="_a8b0b5d5-e2cd-4781-b8fb-e73c18eb43f6" scope="local" type="abcb-glossentry">patient care area</xref> in a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1333_0.4.0.xml#_1f5fbee8-584a-4244-9286-ebf9d8ebb04a" id="_f0afb8f4-e425-4c20-8904-fbf4727fc9d9" scope="local" type="abcb-glossentry">health-care building</xref>; or</li><li>part of an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1251_2.3.0.xml#_9ff8fad7-8992-4708-be17-784d962a0530" id="_a23bd200-6a4f-4df4-8baa-cc75120ac9da" scope="local" type="abcb-glossentry">early childhood centre</xref>, or primary or secondary school, that is used by children; or</li><li>any facility designated for use by people with a disability; or</li></ol></li><li id="_40b181ff-7b82-4388-928a-be45b3c4eee0">not more than 50°C in all other cases.</li></ol></subclause><callout id="_1ead2d1c-5e41-4514-beeb-1358636981c6"><callout-type ncc-info-type="application"/><p>B2D5 applies to all <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1334_0.4.0.xml#_92b3a3dc-59e4-425f-909b-d8eb03e6460a" id="_84540d11-ba4f-4ba7-b770-4ff976379ac2" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">heated water</xref> installations for personal hygiene purposes.</p></callout></clause>