<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_4dbdc27d-d21e-4837-a149-170df1317e78" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 9a"/><facet building="Class 9b"/><facet building="Class 9c"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I3D11</sptc><title id="_fa9ba6de-9d7f-432c-88cf-9ba594ea7855">Portable fire extinguishers</title><archive-num>2019: H3.11</archive-num><subclause id="_d2822d7b-e9dd-4a4d-9f9f-7c0ebce053d4" outputclass="subclause"><title id="_e1b49c95-1680-4e2d-9427-c043aaf42fb6">SubClause</title><num>1</num><p>A <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1271_2.5.0.xml#_f68a626d-6a81-4785-95fa-c032c987c28e" id="_54d1080f-5cb1-4d82-b445-843a945ee3e8" scope="local" type="abcb-glossentry">farm building</xref> not provided with a fire hose reel system in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2612_1.15.0.xml#_628fde10-15f0-43d1-ad76-78e351140e1a" id="_338b9ba6-9f9e-4572-8a85-f12b31c6dd1d" scope="local" type="clause">E1D3</xref> must be provided with—</p><ol outputclass="alpha"><li id="_2891b7ed-239c-4f63-b503-8b6ecfb64c97">one portable fire extinguisher rated at not less than 5ABE in each room containing flammable materials or electrical equipment; and</li><li id="_ff821cdb-62b4-4823-ab31-a6a3a92d5047">one portable fire extinguisher rated at not less than 4A60BE adjacent to every <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_fd6580a7-1205-4d2d-8f5b-4c34e62623ac" scope="local" type="abcb-glossentry">required</xref> <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1263_2.3.0.xml#_9712f630-8cf7-401b-b1cc-ae0be4485915" id="_64b30b18-b564-4d58-9eb3-119ab566d846" scope="local" type="abcb-glossentry">exit</xref> door; and</li><li id="_f51aa5a5-a46f-459a-9da0-4310b63712e5">location signs complying with clauses 3.3 to 3.9 of AS 2444 above each <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_f2d9457c-89c0-4ed2-a719-f87836c1e826" scope="local" type="abcb-glossentry">required</xref> portable fire extinguisher.</li></ol></subclause><subclause id="_99ee0a56-7785-4a98-a888-287a5293bb91" outputclass="subclause"><title id="_46e57dcb-19b7-41af-be42-b69884004995">SubClause</title><num>2</num><p>A <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1272_2.0.0.xml#_9f1c1558-afbd-4a7a-a1b8-ae860e3b2ccd" id="_310e93fc-0419-4ef9-b675-695d38ba3206" scope="local" type="abcb-glossentry">farm shed</xref> must be provided with not less than one portable fire extinguisher for every 500 m<sup id="_599e0074-df7f-4493-bc61-724739357a13">2</sup> of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1314_2.10.0.xml#_7da927fe-453e-424f-b6ec-280f4e464397" id="_5aeb5ba2-3455-4e07-b758-2cbae4af0809" scope="local" type="abcb-glossentry">floor area</xref> or part thereof, distributed as evenly as practicable throughout the building.</p></subclause><subclause id="_080441bf-791e-49d7-8777-83538366a1e8" outputclass="subclause"><title id="_d149c258-c71a-4fa2-b2d2-a9ee71aaaf0b">SubClause</title><num>3</num><p>A portable fire extinguisher <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_726ce173-4e3c-41d1-94e0-8009c2e01ed7" scope="local" type="abcb-glossentry">required</xref> by (2) must be—</p><ol outputclass="alpha"><li id="_8bb43285-7927-4131-ae82-d9653f59dcb5">of ABE type; and</li><li id="_9158d0ff-7679-4f06-846f-2f22c73b1229">not less than 4.5 kg in size; and</li><li id="_2649758c-484e-4deb-8627-6168582325d8">installed in accordance with Section 3 of AS 2444.</li></ol></subclause></clause>