<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_d47a330b-01d8-40a0-9387-8d50ef1bfa46" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 9a"/><facet building="Class 9b"/><facet building="Class 9c"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S20C5</sptc><title id="_3fdf1092-f14b-4b0d-9257-4b31c46417fd">Combined smoke alarm and smoke detection system</title><archive-num>2019: Spec E2.2a: 5</archive-num><subclause id="_2cc424db-19f9-48fa-a342-c527145fb7c8" outputclass="subclause"><title id="_3ff4d49a-a2ad-44cb-bf2a-4f54442fb635">SubClause</title><num>1</num><p>A Class 2 or 3 building or Class 4 part of a building provided with a combination of a smoke alarm system and smoke detection system in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_4fb9883e-9f7d-458e-8f3c-86c68910ed3e" id="_6d142400-9b41-4e83-8162-15bd24959a46" scope="local" type="clause">S20C2</xref> must— </p><ol outputclass="alpha"><li id="_f545a539-860c-48b8-8bc6-13a9ea1a8161">be provided with a smoke alarm system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/667_6.4.0.xml#_994bbd6f-0202-4095-a086-46bf1e15e62a" id="_460896fd-1c88-4f6f-bf6a-5eb3ace1f948" scope="local" type="clause">S20C3</xref> within <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_7e69941d-ab8a-434a-9f4f-6cca68c24ae3" scope="local" type="abcb-glossentry">sole-occupancy units</xref>; and</li><li id="_2e01f151-dc12-4138-8adf-a61274b58599">subject to (2), be provided with a smoke detection system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/669_6.5.0.xml#_7d00be41-a776-4ec4-8755-875554796955" id="_5d2feec1-2a39-47ac-a073-5867561206a2" scope="local" type="clause">S20C4</xref> in areas not within <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_75533330-b4af-45a7-963a-6bb5057107b3" scope="local" type="abcb-glossentry">sole-occupancy units</xref>.</li></ol></subclause><subclause id="_06bf9b01-6ca0-49c3-84a2-c139696f3d33" outputclass="subclause"><title id="_2cc53a1b-db5b-490b-8839-8c436445c3ff">SubClause</title><num>2</num><p>In a Class 2 or 3 building or Class 4 part of a building protected with a sprinkler system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_cf701d35-4f24-404a-a7bc-f98c4ceea8d8" scope="local" type="specification">Specification 17</xref> (other than a FPAA101D or FPAA101H system), smoke detectors are not <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_2c650b3e-15a4-4acd-90d5-7fb75888ec23" scope="local" type="abcb-glossentry">required</xref> in <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1419_4.0.0.xml#_eea79623-bc7d-4ef1-b787-8452b6383ffc" id="_11d925d2-1168-4c73-a01e-9ac79c48c9f1" scope="local" type="abcb-glossentry">public corridors</xref> and other internal public spaces.</p></subclause></clause>