<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_7dad389f-a0e9-42bb-ad33-9ac62783bbda"><num>S35C2l</num><title id="_13aeba53-365e-4b3b-b37e-c2aecac6900f">Internal heat gains for appliances and equipment</title><table id="_1e0dcb30-e608-4b83-8e75-15baff557d4c" keycol="1"><tgroup cols="2"><colspec colname="001" colnum="1" colwidth="216.00*"/><colspec colname="002" colnum="2" colwidth="216.00*"/><thead><row><entry>Application</entry><entry>Internal sensible heat gain rate</entry></row></thead><tbody><row><entry>Class 9a building <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1512_27.0.0.xml#_d1b612a5-df98-4406-ba1e-237f837e1061" id="_165111a6-6e44-40da-b0fb-6f7de50f4aec" scope="local" type="abcb-glossentry">ward area</xref></entry><entry>5 W/m<sup id="_f438d846-c014-49d7-a9b1-7d2cdc24ec48">2</sup> averaged for 24 hours per day, 7 days per week, continuous operation</entry></row><row><entry>Class 8 laboratory and a Class 9a clinic, day surgery and a procedure unit</entry><entry>15 W/m<sup id="_eed64da8-ef14-4f03-9b6e-50845dc3656e">2</sup></entry></row><row><entry>Class 6 shop and shopping centre, Class 6 cafe and restaurant and Class 9b <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1447_0.6.0.xml#_23515733-4511-421a-8c89-650d33e5f6e4" id="_9e625fcf-e3a2-4c84-aa42-ac163e975e2d" scope="local" type="abcb-glossentry">school</xref></entry><entry>5 W/m<sup id="_a9673ed4-77ce-4409-992e-b6555f0531d8">2</sup></entry></row><row><entry>Other applications</entry><entry>No load</entry></row><row><entry>Class 3 (<xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_f999aec6-f57c-495e-8565-33b45eab3a67" scope="local" type="abcb-glossentry">sole-occupancy unit</xref>)</entry><entry>160 W per room</entry></row><row><entry>Class 3 dormitories</entry><entry>No load</entry></row><row><entry>Class 5 building</entry><entry>11 W/m<sup id="_e30aecac-99d7-4ab4-8afc-2b701a271acc">2</sup></entry></row><row><entry>Class 9c building</entry><entry>160 W per room</entry></row><row><entry>Class 9b (conference facilities only)</entry><entry>150 W per room plus 10 W per person</entry></row></tbody></tgroup></table></table-reference>