<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_cba9e43b-6bbd-4cd8-a074-50aa6782f24d" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S31C4</sptc><title id="_1787e0e7-120a-47d9-a7db-f3e5e5f211db">Atrium floor protection</title><archive-num>2019: Spec G3.8: 2.3</archive-num><subclause id="_c350a39b-f3d5-4750-8540-09ae467ac8ba" outputclass="subclause"><title id="_1202a4d5-28f7-4924-bb9c-b9f8456b77f0">SubClause</title><num>1</num><p>The floor of the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1197_1.0.0.xml#_d0042ee6-21cd-4d8c-8873-d8bfb694ceff" id="_46c967b6-e86e-4f6c-b1f5-eb793254f0f5" scope="local" type="abcb-glossentry">atrium</xref> must be protected by sprinklers with—</p><ol outputclass="alpha"><li id="_ffee4feb-0155-46e8-88c0-3ee813ca2410">the use of sidewall pattern sprinkler heads together with overhead sprinklers where dictated by the dimensions of the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1197_1.0.0.xml#_d0042ee6-21cd-4d8c-8873-d8bfb694ceff" id="_0b5a6ce7-1063-418c-8cfb-57398cb92635" scope="local" type="abcb-glossentry">atrium</xref>; and</li><li id="_927022f0-c034-42ed-a6d1-840c9d24db76">sprinkler heads of the quick response type.</li></ol></subclause></clause>