<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_28f1930e-a27c-4a39-9ceb-1d6fa2953824" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>C4D7</sptc><title id="_6f9e0c30-77df-43d6-b37a-fbb3b5a581a1">Sliding fire doors</title><archive-num>2019: C3.6</archive-num><subclause id="_2c0753b1-fade-4bb1-a72d-768254a1cd75" outputclass="subclause"><title id="_417f8463-a509-4965-bb9e-3f12b994501f">SubClause</title><num>1</num><p>If a doorway in a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1301_2.0.0.xml#_0f26abc7-ed98-4bc1-8a36-f3605f035ed5" id="_09d4218d-b4f6-4a32-ba02-a41ba9d4dfe7" scope="local" type="abcb-glossentry">fire wall</xref> is fitted with a sliding fire door which is open when the building is in use—</p><ol outputclass="alpha"><li id="_66e9b552-87e7-402a-a155-56a3623c4b3b">it must be held open with an electromagnetic device, which when de-activated in accordance with (2) and (3), allows the door to be fully closed in not less than 20 seconds and not more than 30 seconds after release; and</li><li id="_c72cf9b3-580e-4d7d-b60b-a4610b3e2bdd">in the event of power failure to the door — the door must fail safe in the closed position in accordance with (a); and</li><li id="_88719247-dcb7-492c-a102-9a32b6bed376">an audible warning device must be located near the doorway and a red flashing warning light of adequate intensity on each side of the doorway must be activated in accordance with (2) and (3); and</li><li id="_d899cac8-c51e-4539-8d73-b435278747b7">signs must be installed on each side of the doorway located directly over the opening stating, in capital letters not less than 50 mm high in a colour contrasting with the background:<signage>WARNING — SLIDING FIRE DOOR</signage></li></ol></subclause><subclause id="_d6c57fa0-3970-4b90-aca7-15f7895dd25a" outputclass="subclause"><title id="_3f9b0fe2-1689-4411-9a74-5a637a803930">SubClause</title><num>2</num><p>The electromagnetic device <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_269a6420-981f-4e68-9bf8-e2a50b87a230" scope="local" type="abcb-glossentry">required</xref> by (1)(a) must be de-activated and the warning system activated by heat or smoke detectors, as appropriate, installed in accordance with AS 1905.1 and the relevant provisions of AS 1670.1.</p></subclause><subclause id="_82ee4dc5-ba35-408e-85df-73f8b731f6c1" outputclass="subclause"><title id="_fa136e6a-78a2-4b9f-86c4-c9aa5edd0f56">SubClause</title><num>3</num><p>Where any other <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_2472d90c-4ed8-45b8-a210-0978ef787452" scope="local" type="abcb-glossentry">required</xref> suitable fire alarm system, including a sprinkler system (other than a FPAA101D system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_30582ee9-34da-4fcd-a8c5-c09685fa38ba" scope="local" type="specification">Specification 17</xref>, is installed in the building, activation in either <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1277_2.0.0.xml#_524b0326-5823-4ddc-9eb3-adab587568e8" id="_5fe927f6-d9b3-4c69-a250-7cca162b0d04" scope="local" type="abcb-glossentry">fire compartment</xref> separated by the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1301_2.0.0.xml#_0f26abc7-ed98-4bc1-8a36-f3605f035ed5" id="_89e84654-a60f-4587-a767-7420d80c733c" scope="local" type="abcb-glossentry">fire wall</xref> must also de-activate the electromagnetic device and activate the warning system.</p></subclause></clause>