<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_d70386ff-3952-4c9e-9cbf-6b1263c5bc27" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S17C11</sptc><title id="_077417ac-97f8-42a3-835d-b90ddedc4222">Sprinkler systems in carparks</title><archive-num>2019: Spec E1.5: 11</archive-num><subclause id="_5c1091af-80f2-42eb-a6d2-9ee138a98116" outputclass="subclause"><title id="_7282f190-0ab5-4593-bd8e-ef81e6c07fa4">SubClause</title><num>1</num><p>A sprinkler system protecting a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1213_1.0.0.xml#_1b0c2237-d3d4-4981-97b8-209936e55520" id="_8bd336fe-c6f1-4565-af63-7a9c1965406e" scope="local" type="abcb-glossentry">carpark</xref> complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/312_17.17.0.xml#_39fc785b-375a-4d7b-8fd0-144b7fededeb" id="_a3773967-3a21-4e38-a37a-fc45d7f3af43" scope="local" type="subclause">S5C19(3)</xref> in a multi-classified building must—</p><ol outputclass="alpha"><li id="_a24bc5cd-4f8e-42de-ba01-6d1d01350cd9">be independent of the sprinkler system protecting any part of the building not used as a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1213_1.0.0.xml#_1b0c2237-d3d4-4981-97b8-209936e55520" id="_23d045aa-1fc4-406f-aad4-ef97553051eb" scope="local" type="abcb-glossentry">carpark</xref>; or</li><li id="_9b8ed294-bda9-42ef-9d52-e5cdb6536716">if forming part of a sprinkler system protecting a part of the building not used as a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1213_1.0.0.xml#_1b0c2237-d3d4-4981-97b8-209936e55520" id="_d057072e-c452-45e7-8dc9-0019d92092c0" scope="local" type="abcb-glossentry">carpark</xref>, be designed such that the section protecting the non-<xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1213_1.0.0.xml#_1b0c2237-d3d4-4981-97b8-209936e55520" id="_89a0175e-df13-44f9-a62a-c61b06e1dcb0" scope="local" type="abcb-glossentry">carpark</xref> part can be isolated without interrupting the water supply or otherwise affecting the effective operation of the section protecting the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1213_1.0.0.xml#_1b0c2237-d3d4-4981-97b8-209936e55520" id="_eba69b4d-5974-4bc4-a4b5-89884afa50c3" scope="local" type="abcb-glossentry">carpark</xref>.</li></ol></subclause></clause>