<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_c373ed8f-0975-46a6-9473-fe8c1f3eacc1" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S17C10</sptc><title id="_fea3e69a-b1c5-408d-ab81-15e4500b5b36">Anti-tamper devices</title><archive-num>2019: Spec E1.5: 10</archive-num><subclause id="_94baaf30-b156-4eb5-a6ce-8a50638bd59b" outputclass="subclause"><title id="_b51a900d-8c54-46e2-8ca9-01b08461ebb0">SubClause</title><num>1</num><p>Where a sprinkler system is installed—</p><ol outputclass="alpha"><li id="_a5854603-25d9-4898-9f6f-ae6205ef752d">over any <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_1726f216-7f72-4152-9d7e-43d1789ba950" scope="local" type="abcb-glossentry">stage</xref> area in a theatre, public hall or the like, visual and audible status indication of sprinkler valves must be provided at the location normally used by the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_c011bbff-0da6-4f2e-9f97-b1c2d4878b38" scope="local" type="abcb-glossentry">stage</xref> manager; or</li><li id="_3254386e-5109-430c-8701-735504a853b4">in a space housing lift electrical and control equipment (including machine rooms, secondary floors and sheave rooms), any valves provided to control sprinklers in these spaces must be located adjacent to the space.</li></ol></subclause><subclause id="_bbea360b-0ed8-4164-8795-23bffee77340" outputclass="subclause"><title id="_36ccc4df-fd8f-473e-bece-7660d7fb48ea">SubClause</title><num>2</num><p>Any valves provided to control sprinklers required by (1) must be fitted with anti-tamper monitoring devices connected to a monitoring panel.</p></subclause></clause>