<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_c0f81e37-c446-44bb-a00a-2c6b67610ee0" outputclass="ncc-clause" variation="NT"><sptc>E1D10</sptc><title id="_7aa55d4b-798b-4249-81ed-99c1ea93291b">Where sprinklers are required: Class 9a and 9c buildings</title><archive-num>2019: NT Table E1.5</archive-num><subclause id="_997cebe2-d60d-496e-b204-7bc8b6d513b7" outputclass="subclause"><title id="_e92223da-232c-429d-8815-c621423d87c2">SubClause</title><num>1</num><p>In a Class 9a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1333_0.4.0.xml#_1f5fbee8-584a-4244-9286-ebf9d8ebb04a" id="_6ccfc746-0695-45b2-a894-37edbd10981f" scope="local" type="abcb-glossentry">health-care building</xref> used as a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1436_4.0.0.xml#_b286ccd1-342e-49e1-95e9-4b6a0a6c0447" id="_797496b7-66a6-490c-9ad3-65806fe51fdb" scope="local" type="abcb-glossentry">residential care building</xref>, sprinklers are <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_87a99c43-19f8-4248-909f-a20ba4ad04f4" scope="local" type="abcb-glossentry">required</xref> throughout the building and in any <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1277_2.0.0.xml#_524b0326-5823-4ddc-9eb3-adab587568e8" id="_f4053b0e-6944-4afe-a83e-0ae4402578b2" scope="local" type="abcb-glossentry">fire compartment</xref> containing a Class 9a part used for residential care.</p></subclause><subclause id="_083b1acb-9e5a-4164-9e8f-a5b1d9614c0e" outputclass="subclause"><title id="_02e1655c-2f10-47d8-962b-af66ce0a7abe">SubClause</title><num>2</num><p>In a Class 9a building, other than as described in (1), sprinklers are <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_d58ed567-5f81-4678-bbbf-aa9426ab9b8d" scope="local" type="abcb-glossentry">required</xref> if the building has more than one <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1483_25.0.0.xml#_53ff3ea1-55e7-4f2a-b2b3-ca445ff64c15" id="_d094762c-24d8-4efd-ab79-640663195363" scope="local" type="abcb-glossentry">storey</xref>.</p></subclause><subclause id="_8860fccf-2742-4c8c-ac7e-94b6127be6f3" outputclass="subclause"><title id="_8907ff45-6be2-4053-b094-3984c0bdd396">SubClause</title><num>3</num><p> In a Class 9c building, sprinklers are <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_dc18747f-1f8e-41d1-a8b5-909b29c1c970" scope="local" type="abcb-glossentry">required</xref> throughout the building and in any <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1277_2.0.0.xml#_524b0326-5823-4ddc-9eb3-adab587568e8" id="_b28b4de9-512c-4367-9c92-bb1bb40566d1" scope="local" type="abcb-glossentry">fire compartment</xref> containing a Class 9c part.</p></subclause></clause>