<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_91413b5a-2b61-4670-a533-6df74aedec14" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>F6D10</sptc><title id="_f2cf2de2-8dba-4e84-9d74-bd5a571b7d60">Airlocks</title><archive-num>2019: F4.9</archive-num><subclause id="_95c10cbc-b19e-4b50-9a99-93b0689dd610" outputclass="subclause"><title id="_4dec17fe-2bed-438a-bfcb-7d58f05ede8b">SubClause</title><num>1</num><p>If a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1445_0.13.0.xml#_b30a308f-eb9f-4549-a6c1-19d5f32a5272" id="_00b0bd23-0527-4f21-893f-d70ea3269b99" scope="local" type="abcb-glossentry">sanitary compartment</xref> is prohibited under <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2828_2.4.0.xml#_78145f23-48cb-4e94-921e-73b3c530ae53" id="_0c28f905-4d61-481e-bf34-221358299c37" scope="local" type="clause">F6D9</xref> from opening directly to another room—</p><ol outputclass="alpha"><li id="_f060f000-de44-4edb-84b0-397f111b8817">in a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_b05faa55-b54b-47a0-97f7-9868e690e73d" scope="local" type="abcb-glossentry">sole-occupancy unit</xref> in a Class 2 or 3 building or Class 4 part of a building—<ol><li>access must be by an airlock, hallway or other room; or</li><li>the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1445_0.13.0.xml#_b30a308f-eb9f-4549-a6c1-19d5f32a5272" id="_055b914e-8693-4fe1-ada4-de561172f890" scope="local" type="abcb-glossentry">sanitary compartment</xref> must be provided with mechanical exhaust ventilation; and</li></ol></li><li id="_922adbae-aeed-4f2d-b52e-2f5f79208346">in a Class 5, 6, 7, 8 or 9 building (which is not an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1251_2.3.0.xml#_9ff8fad7-8992-4708-be17-784d962a0530" id="_b8caaff0-1abe-49a6-9707-ae92120efb7f" scope="local" type="abcb-glossentry">early childhood centre</xref>, primary <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1447_0.6.0.xml#_23515733-4511-421a-8c89-650d33e5f6e4" id="_ecdd8c2b-d3c8-460a-83e9-146391814318" scope="local" type="abcb-glossentry">school</xref> or <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1386_0.4.0.xml#_0403e22a-286f-4b36-b369-af068221632b" id="_53000dde-bfff-4053-b61e-a05acc1c68eb" scope="local" type="abcb-glossentry">open spectator stand</xref>)—<ol><li>access must be by an airlock, hallway or other room with a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1314_2.10.0.xml#_7da927fe-453e-424f-b6ec-280f4e464397" id="_cde692be-e7d3-4bb3-9be8-c0d6cc6c01fa" scope="local" type="abcb-glossentry">floor area</xref> of not less than 1.1 m<sup id="_484913c3-6c14-42e2-b4a0-185036f91ab3">2</sup> and fitted with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1449_26.3.0.xml#_7f0d37c8-f244-4a83-9a76-6ece85e1e430" id="_f8f516e9-83e6-49cd-b8e0-4270318617a5" scope="local" type="abcb-glossentry">self-closing</xref> doors at all access doorways; or</li><li>the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1445_0.13.0.xml#_b30a308f-eb9f-4549-a6c1-19d5f32a5272" id="_7dbbbd96-cb75-4bc5-97c1-0cf6cb6dfc8e" scope="local" type="abcb-glossentry">sanitary compartment</xref> must be provided with mechanical exhaust ventilation and the doorway to the room adequately screened from view.</li></ol></li></ol></subclause></clause>