<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_ebcde7af-5fac-4ef2-85d0-e207606a85b6" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S43C11</sptc><title id="_86864fa3-1881-4f75-8477-03661ea067ab">Supply of water for fire-fighting purposes</title><archive-num>New for 2022</archive-num><clause-variation href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/7635_0.1.0.xml" variation="NSW" variation-type="REPLACE">NSW REPLACE Clause</clause-variation><subclause id="_fcf36748-f345-4a90-a138-ea969b932b29" outputclass="subclause"><title id="_322fb5b4-633c-464f-a6da-66706e048022">SubClause</title><num>1</num><p>Water for fire-fighting purposes must be available and consist of—</p><ol outputclass="alpha"><li id="_c2954530-4f5b-465b-8a99-c4eca5bc18a3">a fire hydrant system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2608_1.15.0.xml#_5234c962-ded1-4278-8b92-820a4803de16" id="_e6d661e4-3472-4e2d-a5ca-a8c690e64549" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">E1D2</xref>, or</li><li id="_0141d2cc-7c88-4798-aa0f-f3b7b68b7612">a static water supply consisting of tanks, <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1487_0.7.0.xml#_4cbd9e00-0622-4dfd-9de4-913c80257732" id="_7ec8755f-3a83-430e-8b33-0b7005d531b3" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">swimming pools</xref>, dams or the like, or a combination of these, together with suitable pumps, hoses and fittings, capable of providing the required flow rate for a period of not less than 4 hours, determined in consultation with the relevant <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1275_0.4.0.xml#_cc69b717-0915-4071-87d9-176353f8cc9a" id="_c69331ed-f469-4000-92f6-8d6a340f5a42" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">fire brigade</xref>.</li></ol></subclause></clause>