<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_babb54f8-d1d5-41db-b25a-c2725d43085f" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S19C7</sptc><title id="_cc0cfd0a-316f-49f2-9902-cc2e8bd74a73">Construction of a fire control room</title><archive-num>2019: Spec E1.8: 6</archive-num><subclause id="_c7c36230-5c60-4fb9-8d90-94110d7269d1" outputclass="subclause"><title id="_d14c9b5e-9200-4051-9ac9-83194b25e54c">SubClause</title><num>1</num><p>A fire control centre in a building more than 50 m in <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1252_2.0.0.xml#_cd986c21-bc64-43a9-954d-86e35d335b74" id="_865db8ed-5631-4a3a-8900-4d48eb8ed267" scope="local" type="abcb-glossentry">effective height</xref> must be in a separate room where—</p><ol outputclass="alpha"><li id="_518a7a8e-355b-4ca7-a9ab-dd08f18b09ed">the enclosing construction is of concrete, masonry or the like, sufficiently impact resistant to withstand the impact of any likely falling debris, and with an FRL of not less than 120/120/120; and</li><li id="_22c5c4de-23a1-498a-895c-cda555212732">any material used as a finish, surface, lining or the like within the room complies with the requirements of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/145_0.3.0.xml#_e9a243a2-bb82-477d-96de-79af1512dd05" id="_ad33c017-b6f2-4228-9efb-ca4ca4e1668b" scope="local" type="specification">Specification 7</xref>; and</li><li id="_285618bc-d020-4964-9826-85368d732752">services, pipes, ducts and the like that are not directly <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_fec88ae8-5b28-40dd-b494-f7288b2b904f" scope="local" type="abcb-glossentry">required</xref> for the proper functioning of the fire control room do not pass through it; and</li><li id="_32b59f31-2b2b-4949-8079-a764a036e426">openings in the walls, floors or ceiling which separate the room from the interior of the building are confined to doorways, ventilation and other openings for services necessary for the proper functioning of the facility.</li></ol></subclause></clause>