<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_3bf81929-3c2c-4184-965c-391dcdf4c56f" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S7C3</sptc><title id="_2ff033e4-5b12-4fed-b304-eaa5c58ac182">Floor linings and floor coverings</title><archive-num>2019: Spec C1.10: 3</archive-num><subclause id="_614c65ca-f0aa-4444-99f6-7e521815417b" outputclass="subclause"><title id="_116f2ff8-8072-4023-aeaa-3b4591c35df1">SubClause</title><num>1</num><p>A floor lining or floor covering must have—</p><ol outputclass="alpha"><li id="_d275d9cf-73ed-4a56-8cbd-3112d5ebc87b">a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1232_0.7.0.xml#_a79820ca-7f44-4362-bffa-251cb62fd2c3" id="_ef1dd58c-fbcf-4c0a-82a0-52d20ba44586" scope="local" type="abcb-glossentry">critical radiant flux</xref> not less than that listed in <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/224_23.1.0.xml#_744a4185-36b6-4379-bed9-1f8546bb5d74" id="_fb557142-22f0-45f6-b129-a76a266dbd17" referencetype="Text" scope="local" synctargettext="false" type="table-reference">Table S7C3</xref>; and</li><li id="_4706e23d-fb7e-4eb1-988f-40c93e63a201">in a building not protected by a sprinkler system (other than a FPAA101D or FPAA101H system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_d91c31aa-83e4-49b8-9ecc-60a52b897828" scope="local" type="specification">Specification 17</xref>, a maximum <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1470_0.5.0.xml#_2a818067-2778-48dd-bcc2-a630dcf39fd7" id="_1efdad6c-39a6-477c-9543-df10e77fafe4" scope="local" type="abcb-glossentry">smoke development rate</xref> of 750 percent-minutes; and</li><li id="_88179746-f704-4f52-bdc7-b8ddaa9f423c">a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1324_2.0.0.xml#_98b60468-48ff-40b6-9c9a-57b1ad3cd803" id="_b07921ed-0a94-4dec-aeee-b30543fd7bc5" scope="local" type="abcb-glossentry">g</xref><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1324_2.0.0.xml#_98b60468-48ff-40b6-9c9a-57b1ad3cd803" id="_b07921ed-0a94-4dec-aeee-b30543fd7bc5" scope="local" type="abcb-glossentry">roup number</xref> complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/512_22.2.0.xml#_53d6ff69-b06f-4afb-a2fb-17ccc282d031" id="_08e23bc6-d196-439a-8048-2033f1dab9a2" scope="local" type="clause">S7C6(b)</xref>, for any portion of the floor covering that is continued more than 150 mm up a wall.</li></ol></subclause><table-reference conref="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/224_23.1.0.xml" graph="None" id="_744a4185-36b6-4379-bed9-1f8546bb5d74"><num/><title id="_0da2c33f-ff80-44db-9870-f1e09f5fc408"/></table-reference></clause>