<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_a53bd401-41af-47d7-9913-87c1696853ab" variation="TAS"><num>I4D18b</num><title id="_066889e4-c595-4689-84a1-9f1476974279">Drainage from cooling units within refrigerated chambers or cooling chambers</title><table id="_05a821c0-09dc-41ee-b402-44aaee18edbc" keycol="1"><tgroup cols="2"><colspec colname="001" colnum="1" colwidth="216.00*"/><colspec colname="002" colnum="2" colwidth="216.00*"/><thead><row><entry>Cooling unit type</entry><entry>Drainage requirements</entry></row></thead><tbody><row><entry>Wall-mounted</entry><entry>Drain water must be contained and removed by either a wall-mounted channel or a spoon drain located under the coil.</entry></row><row><entry>Floor-mounted</entry><entry>Drain water must be confined by kerbs, of a height not less than 150 mm, and directed to a trapped drain outlet.</entry></row><row><entry>Ceiling-mounted</entry><entry>Drain water must be confined by suitable insulated drip trays directly connected to the drainage system.</entry></row></tbody></tgroup></table></table-reference>