<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_01c1583a-5c6c-49d1-b871-4e23c5eb0ff5" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S43C12</sptc><title id="_c7e01dcf-805a-4164-9790-55bd468f2238">Emergency power supply</title><archive-num>New for 2022</archive-num><subclause id="_03097854-3f24-4f4e-8141-303ecbb9d621" outputclass="subclause"><title id="_65985476-78f5-46cc-89a5-2df96ea31737">SubClause</title><num>1</num><p>Emergency power must be provided to support, for not less than 4 hours before and 2 hours after the passing of the fire front during a bushfire event, the ongoing operation of—</p><ol outputclass="alpha"><li id="_375a14dc-cbc8-42f1-957e-2e09c3b6e337">air handling systems to maintain internal tenability; and</li><li id="_3c2fe647-02b6-4f32-a5f5-6870b3a621dc">any pumps for fire-fighting; and</li><li id="_0ad3ad24-e351-4b69-a0db-bbc13c447718">any emergency lighting and <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1263_2.3.0.xml#_9712f630-8cf7-401b-b1cc-ae0be4485915" id="_ef1edd35-2f39-416d-a44c-5cb607ecf968" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">exit</xref> signs; and </li><li id="_055da362-87ae-49e8-8851-35fc56eda2eb">any other emergency equipment listed in <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1310_1.3.0.xml#_2816e85f-0f4f-455b-9b25-76dac2729846" id="_3008164b-56a1-4f48-a780-88357645d11d" referencetype="Text" scope="local" synctargettext="false" type="subclause">C3D14(6)</xref> and <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_a5b45a91-1ac3-44a8-8644-acfc09c225a9" id="_922cafe8-e651-4228-8fd4-e96cd5008bae" referencetype="Text" scope="local" synctargettext="false" type="glossterm">required</xref> to be provided.</li></ol></subclause><subclause id="_3e13d447-c43a-4a00-b238-2aa267028dc9" outputclass="subclause"><title id="_aa99389f-c05a-4406-988a-3d88085e2e67">SubClause</title><num>2</num><p>Manual control for emergency back-up power supply must be provided to facilitate manual intervention where the power supply fails or runs out.</p></subclause></clause>