<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_e1f5d3b6-8e5e-45ab-b7f9-4ec6dc54a062" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S43C3</sptc><title id="_9b9d3bfa-a1e9-4ac5-98b3-4c47c80ed818">Separation between buildings</title><archive-num>New for 2022</archive-num><subclause id="_e4926512-1e68-47a6-97ed-e82ad02a09b1" outputclass="subclause"><title id="_a16f7611-d0a8-465a-bc15-7b3983ae075c">SubClause</title><num>1</num><p>The building must be located not less than 12 m from any other building. </p></subclause><subclause id="_6c99d2b3-a94d-413a-a744-c70dbe44baae" outputclass="subclause"><title id="_0f8d5327-4e94-4370-b97f-5bef8239fbc7">SubClause</title><num>2</num><p>The separation distance <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_a5b45a91-1ac3-44a8-8644-acfc09c225a9" id="_5220ff7f-6449-42cf-99ac-090009574e6f" referencetype="Text" scope="local" synctargettext="false" type="glossterm">required</xref> by (1) need not be complied with if the building is constructed—</p><ol outputclass="alpha"><li id="_7993abe2-492c-4c2b-b5d1-68e78b394093">with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_694b7f8b-ea66-4317-98bc-1bc0bba5f7d0" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> that have an FRL of not less than 60/60/60 when tested from the outside, including any openings protected in accordance with AS 3959 for BAL—19 or greater; or</li><li id="_b7ee0179-50b5-48c8-b40b-8f24c352b78b">for <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_f9d0ac4d-932c-4469-b2b4-0a16a08cdb08" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> and roof, using a material or system that satisfies the test criteria of AS 1530.8.1 for a radiant heat flux of 10 kW/m² or greater.</li></ol></subclause></clause>