<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_1d3a91b4-d72b-43f6-8f7f-a23193547abc" outputclass="ncc-clause" variation="NSW"><sptc>S43C11</sptc><title id="_1f52bd64-6e10-431d-9343-b44137706138">Supply of water for fire-fighting purposes</title><archive-num>New for 2022</archive-num><subclause id="_4cd82dbc-1ec5-4a58-8c06-3f7fe573bce7" outputclass="subclause"><title id="_cceab7ff-f8ae-4ee1-a6e3-b575f20399fa">SubClause</title><num>1</num><p>Water for fire-fighting purposes must be available and consist of—</p><ol outputclass="alpha"><li id="_6d77c02d-608c-4784-bf57-de952be97a65">A fire hydrant system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2608_1.15.0.xml#_5234c962-ded1-4278-8b92-820a4803de16" id="_1faafc14-5c20-470e-bbe9-731a60bdfd2b" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">E1D2</xref>; or</li><li id="_4106b044-fbd2-4c85-86d2-f1132af96571">A static water supply consisting of tanks, <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1487_0.7.0.xml#_fdffe6e3-cc05-474b-9b90-e89a04249c30" id="_dd03a3a8-aa48-4158-904d-8e28f7ca9bab" referencetype="Text" scope="local" synctargettext="false" type="glossterm">swimming pools</xref>, dams or the like, or a combination of these, together with suitable pumps, hoses and fittings, determined in consultation with the relevant <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1275_0.4.0.xml#_a5d1dbce-b039-4907-a73f-de976e4b2cb3" id="_2f7189d9-92bc-4363-af7f-2ce5810c650c" referencetype="Text" scope="local" synctargettext="false" type="glossterm">fire brigade</xref> that—<ol><li id="_446c4e08-7803-41d5-b5ee-d737b64d4593">is capable of providing the required flow rate for a period of not less than 4 hours; or</li><li>has a volume of 10 000 litres for each occupied building.</li></ol></li></ol></subclause></clause>