<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_785e395a-703b-4da2-b1f9-27284ff5af75" outputclass="ncc-clause" variation="NSW"><sptc>J1P1</sptc><title id="_75a091e2-9d64-43bf-a739-2cc859aa25df">Energy use</title><archive-num>2019: JP1</archive-num><subclause id="_8cc873f8-78cd-47e7-b5b5-99f6cb07d103" outputclass="subclause"><title id="_6f8a9de8-b102-494a-ba7b-33773125307d">SubClause</title><num>1</num><p>A building including its <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1456_25.0.0.xml#_242ba975-4cdf-4b84-9f41-b8d524ee17c2" id="_3c5df5c8-79c9-4a8b-bdda-61f754adb3da" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">services</xref>, must have features that facilitate the efficient use of energy appropriate to—</p><ol outputclass="alpha"><li id="_708b494d-7372-48a9-b997-8c4f720b8f38">the function and use of the building; and</li><li id="_16398544-ad87-4803-90c3-15c1892a0484">the level of human comfort required for the building use; and</li><li id="_4fc333c4-5cf2-4c51-8ba7-0f78c14fa4e5">solar radiation being—<ol><li>utilised for heating; and</li><li>controlled to minimise energy for cooling; and</li></ol></li><li id="_a0ca31cf-9c1a-43da-8e51-c72fcaa842c8">the energy source of the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1456_25.0.0.xml#_242ba975-4cdf-4b84-9f41-b8d524ee17c2" id="_3fdac6cf-204d-4f7e-bdb7-1d12d8a686ae" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">services</xref>; and</li><li id="_7e4a630d-2900-4fd3-894a-5d96e3e66cd4">the sealing of the building <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1259_2.9.0.xml#_71ea06f9-79ec-4eae-bdf4-d90302f51eb5" id="_97d98cc4-7237-4c74-bf16-629497598d59" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">envelope</xref> against air leakage; and</li><li id="_bcc0e155-0984-466f-b88a-a4d95155d42b">for a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1225_1.5.0.xml#_26276791-20ad-4404-951f-29b5bff0ff80" id="_79512e39-3b99-4f39-a2d3-c8566971ae18" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">conditioned space</xref>, achieving an hourly <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1429_4.0.0.xml#_044c235a-5f51-4bc7-9eb9-7cfba1a0f023" id="_28a960dd-61de-4784-aba0-921d43602f60" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">regulated energy</xref> consumption, averaged over the annual <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1341_0.5.0.xml#_22178a20-4ed7-4cee-8507-b36346202638" id="_f77c255b-9ecf-417a-8f2c-8a7fa9bd96d5" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">hours of operation</xref>, of not more than—<ol><li>for a Class 6 building, 80 kJ/m².hr; and</li><li>for a Class 5, 7b, 8 or 9a building other than a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1512_27.0.0.xml#_d1b612a5-df98-4406-ba1e-237f837e1061" id="_596fa3b8-643e-4263-b55d-edcf36aff6de" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">ward area</xref>, or a Class 9b <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1447_0.6.0.xml#_23515733-4511-421a-8c89-650d33e5f6e4" id="_b2b4052f-b20f-4bc8-9697-be4cff3057c4" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">school</xref>, 43 kJ/m².hr; and</li><li>for all other building classifications, 15 kJ/m².hr.</li></ol></li></ol></subclause><callout id="_0f50b079-92c2-412e-8323-58fa20685751"><callout-type ncc-info-type="application"/><p>NSW J1P1 does not apply to a Class 2 building or a Class 4 part of a building.</p></callout></clause>