<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_e04d2918-4af8-4338-9726-edc52eb14247"><num>J6D9a</num><title id="_73f9f537-8e79-48df-9dc6-df70afdb49e8">Piping — Minimum insulation R-Value</title><table id="_23ec88b0-8d76-4aa0-a54e-f6db688c3d56" keycol="1"><tgroup cols="5"><colspec colname="001" colnum="1" colwidth="86.40*"/><colspec colname="002" colnum="2" colwidth="86.40*"/><colspec colname="004" colnum="3" colwidth="86.40*"/><colspec colname="005" colnum="4" colwidth="86.40*"/><colspec colname="003" colnum="5" colwidth="86.40*"/><thead><row><entry>Fluid temperature</entry><entry>Minimum insulation  <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1420_0.4.0.xml#_e5acb40f-3d3d-4a3d-8987-f09f7eaadf77" id="_d19ba02b-ed7c-4edf-9ea2-b9cd9b9374ee" scope="local" type="abcb-glossentry">R-Value</xref> nominal pipe diameter ≤ 40 mm</entry><entry>Minimum insulation <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1420_0.4.0.xml#_e5acb40f-3d3d-4a3d-8987-f09f7eaadf77" id="_c3c2e24c-aeb5-4b3d-9a70-c079e47b2ccf" scope="local" type="abcb-glossentry">R-Value</xref> — nominal pipe diameter &gt; 40 mm and ≤ 80 mm</entry><entry>Minimum insulation <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1420_0.4.0.xml#_e5acb40f-3d3d-4a3d-8987-f09f7eaadf77" id="_b26efaf6-1d8d-4a85-a6fa-79799297c3c2" scope="local" type="abcb-glossentry">R-Value</xref> — nominal pipe diameter between &gt; 80 mm and ≤ 150 mm</entry><entry>Minimum insulation <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1420_0.4.0.xml#_e5acb40f-3d3d-4a3d-8987-f09f7eaadf77" id="_6ac6a562-9538-47f9-8991-1baf15bbd18e" scope="local" type="abcb-glossentry">R-Value</xref> — nominal pipe diameter &gt; 150 mm</entry></row></thead><tbody><row><entry>Low temperature chilled — ≤ 2°C</entry><entry>1.3</entry><entry>1.7</entry><entry>2.0</entry><entry>2.7</entry></row><row><entry>Chilled — &gt; 2°C but ≤ 20°C</entry><entry>1.0</entry><entry>1.5</entry><entry>2.0</entry><entry>2.0</entry></row><row><entry>Heated — &gt; 30°C but ≤ 85°C</entry><entry>1.7</entry><entry>1.7</entry><entry>1.7</entry><entry>1.7</entry></row><row><entry>High Temperature heated — &gt; 85°C</entry><entry>2.7</entry><entry>2.7</entry><entry>2.7</entry><entry>2.7</entry></row></tbody></tgroup></table><desc-note id="_bc2b4033-3a2e-48f8-b4ff-299f64040070"><p>The minimum <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_db6b3ac5-62a4-40ff-b289-51e393f7dc02" inv:access="external" scope="local" type="abcb-glossentry">required</xref> <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1420_0.4.0.xml#_e5acb40f-3d3d-4a3d-8987-f09f7eaadf77" id="_7756a1ca-aef4-4555-b923-99e4fb155ad2" inv:access="external" scope="local" type="abcb-glossentry">R-Value</xref> may be halved for <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1399_0.5.0.xml#_83695a00-3a6b-4a83-b26a-9faa46d4e1dc" id="_3577fbe6-c167-44c3-9e8e-c4f355c0e20e" inv:access="external" scope="local" type="abcb-glossentry">piping</xref> penetrating a structural member.</p></desc-note></table-reference>