<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_3b4a9a3b-3f07-4b1b-9650-9175d67e8b32" outputclass="ncc-clause" variation="NSW"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D51</sptc><title id="_6258935f-58bd-4c4d-823d-4acefc2fb5d7">Electric mains installation: main switchboard</title><archive-num>2019: NSW H101.19.1</archive-num><subclause id="_7364b822-0eac-471d-8184-aff21987f232" outputclass="subclause"><title id="_31cf7aea-1530-4a70-a62d-3d68c39c05d8">SubClause</title><num>1</num><p>The switchboard containing the main isolation switch must—</p><ol outputclass="alpha"><li id="_1754c30a-e0ed-478c-9e53-da95562b6103">be located in a position that is readily accessible to authorised persons, and to the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1275_0.4.0.xml#_cc69b717-0915-4071-87d9-176353f8cc9a" id="_75061b41-9959-4c30-993f-9023cabab6f1" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">fire brigade</xref> in the case of an emergency; and</li><li id="_2a78531a-3476-400e-b54d-c022060d7f18">be enclosed by construction having an FRL of not less than 60/60/60.</li></ol></subclause></clause>