<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_f4f3055b-cfd7-416a-80ff-6cf16cdd44e4" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 9a"/><facet building="Class 9b"/><facet building="Class 9c"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S23C8</sptc><title id="_cba01942-efc5-42d0-8b25-dc9c0fff7b14">Connection to monitoring service</title><archive-num>2019: Spec E2.2d: 3(a)</archive-num><subclause id="_9a7f68d2-fef5-41d4-b37d-d27b7be8158b" outputclass="subclause"><title id="_b716f7cc-4080-4baa-8447-b68a6688706c">SubClause</title><num>1</num><p>Connection of a residential sprinkler system to a fire station or other approved monitoring service must be via a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1477_0.8.0.xml#_447d0dbd-037c-4669-9710-fc54d51cf1c0" id="_544c8794-9148-4d3e-a400-6b275f73a674" scope="local" type="abcb-glossentry">sprinkler alarm switch</xref>, connected to alarm signalling equipment.</p></subclause><subclause id="_ddd05387-6b9d-4f15-b150-a4b66665f6af" outputclass="subclause"><title id="_3db78fcf-3a09-4d95-93e3-e09a71f4b7ee">SubClause</title><num>2</num><p>The connection from the alarm signalling equipment must be in accordance with AS 1670.3.</p></subclause><subclause id="_45ef9bce-b596-4824-9df6-413df1817985" outputclass="subclause"><title id="_bf7b8700-c8dd-47fb-9e19-3ba13cd7b837">SubClause</title><num>3</num><p>The alarm signalling equipment must be installed—</p><ol outputclass="alpha"><li id="_f1a281f9-5b2f-4cc2-8138-d18fa5c6fba2">in a secure, accessible position; and</li><li id="_948eb5c7-a6a3-45ed-852a-488bcdf03218">in a weatherproof housing, if located externally; and</li><li id="_6df75139-7030-4a3b-b2e1-6fd85485231e">not more than 500 mm from the system flow switch.</li></ol></subclause></clause>