<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_5a5ac4b8-382d-4f5a-975c-b3147e513a63" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S43C5</sptc><title id="_71b2df37-22de-4a94-b69c-34549898533c">Separation from hazards</title><archive-num>New for 2022</archive-num><subclause id="_2c278907-3cdf-46e6-b349-4e573a064f6b" outputclass="subclause"><title id="_dbaf761c-304b-4166-99d7-6f8297b6cf63">SubClause</title><num>1</num><p>The <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_4d16234b-5e0e-4708-b577-f2d7a06016e2" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> and roof of the building must be protected from potential hazards on the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1463_0.4.0.xml#_6541804e-8051-484a-83ae-58240227645b" id="_c5e7fc8d-ce1d-401c-a863-ef699c726d54" referencetype="Text" scope="local" synctargettext="false" type="glossterm">site</xref> such as liquefied petroleum gas bottles, fuel storage, storage of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1221_0.9.0.xml#_a7b1bb43-dc94-41fb-9e49-6a37f0d6b236" id="_62f248ca-f070-40fd-88b6-9e9006d36866" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">combustible</xref> materials, waste bins, vehicles, machinery, and the like, by—</p><ol outputclass="alpha"><li id="_874a17b6-40fc-4baf-af62-241a2472fe2f">a separation distance of not less than 10 m; or</li><li id="_327bd51a-b639-4e16-b13f-c78915e22bbf">where within the 10 m separation distance described in (a), constructed with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_7fc9f9af-0518-4c17-a890-3274201dbb6d" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> that have an FRL of not less than 60/60/60 when tested from the outside, including any openings protected in accordance with AS 3959 for BAL—19 or greater; or </li><li id="_5cdc1564-34d2-43a0-a55a-e62d6e53e798">for <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_63902c9d-d573-4ba5-af50-7e2c09650802" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> and roof, using a material or system that satisfies the test criteria of AS 1530.8.1 for a radiant heat flux of 10 kW/m² or greater. </li></ol></subclause></clause>