<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_c543128f-0526-41c7-baff-1fec039f1b6f" outputclass="ncc-clause"><sptc>B1P<xt:insText xt:action="start" xt:author="Jerome Samuel" xt:dateTime="2024-08-26T09:18:00" xt:id="5adde763-0040-4cf6-85c7-04a9fa6f71c7"/>6<xt:insText xt:action="end" xt:id="5adde763-0040-4cf6-85c7-04a9fa6f71c7"/><xt:delText xt:action="start" xt:author="Jerome Samuel" xt:dateTime="2024-08-26T09:18:00" xt:id="6f2e3a00-27eb-4822-8b24-f1ba8a7dcd1c"/>5<xt:delText xt:action="end" xt:id="6f2e3a00-27eb-4822-8b24-f1ba8a7dcd1c"/></sptc><title id="_b5d4e331-1ad3-4914-832b-dfcbc834d2bc">Pressure</title><archive-num>2019: BP1.2</archive-num><clause-variation href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/7187_0.6.0.xml" variation="TAS" variation-type="REPLACE">TAS REPLACE Clause</clause-variation><subclause id="_c7080e11-40c4-4285-ac7e-27e0604f4402" outputclass="subclause"><title id="_4f23caaf-ebc9-45c4-bb8f-81462935f49a">SubClause</title><num>1</num><p>The points of discharge for a cold water service must—</p><ol outputclass="alpha"><li id="_2b99f263-92f9-4626-acc2-c0c397aff2c3">have—<ol outputclass="alpha"><li>a working pressure of not less than 50 kPa; and</li><li>a static pressure within the building of not more than 500 kPa; or </li></ol></li><li id="_bb12a96b-bbef-4409-82d2-f5cef8a6443c">have water pressures suitable for the correct functioning of the fixture or appliance where water pressures outside of (a)(i) and (a)(ii) are required.</li></ol></subclause></clause>