<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_e13bbd89-c146-4e6d-b322-76c02a7449d8" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 9a"/><facet building="Class 9c"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>E2D16</sptc><title id="_7a00d14f-2d23-46c0-853a-068485386a77">Class 9b – assembly buildings: nightclubs, discotheques and the like</title><archive-num>2019: Table E2.2b</archive-num><clause-variation href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/4259_2.3.0.xml" variation="NSW" variation-type="REPLACE">NSW REPLACE Clause</clause-variation><subclause id="_bb5e2719-3436-45ff-a4c8-264a1f5b8759" outputclass="subclause"><title id="_696d1162-0a16-4ff0-953b-29702ac357df">SubClause</title><num>1</num><p>A Class 9b <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1195_1.0.0.xml#_367d20c3-85f7-45e8-ad37-bba3e069f07d" id="_a65aabb4-071e-4549-af10-09b37dfba63e" scope="local" type="abcb-glossentry">assembly building</xref> which is a nightclub, discotheque or the like must be provided with—</p><ol outputclass="alpha"><li id="_13694b42-1a18-4680-94b6-fcec3ffe6427"><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_62842778-5f78-42f5-99fa-df68d40b8596" scope="local" type="abcb-glossentry">automatic</xref> shutdown of any air-handling system (other than miscellaneous exhaust air systems installed in accordance with Sections 5 and 6 of AS 1668.1) which does not form part of the smoke hazard management system, on the activation of—<ol><li>smoke detectors installed complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/672_7.5.0.xml#_38696b94-36c5-42a0-a851-78ecd6b31308" id="_95995488-6044-4e81-8738-66bf38d1a388" scope="local" type="clause">S20C6</xref>; and</li><li>any other installed fire detection and alarm system, including a sprinkler system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_88a1b54f-49ef-4812-93ae-5f8d20485726" scope="local" type="specification">Specification 17</xref>; and</li></ol></li><li id="_c066e8a7-9bcc-45b0-9b86-2433047b3df6">at least one of the following:<ol><li>An <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_6fe3f952-0322-423a-920e-4f5f9cc0b3eb" scope="local" type="abcb-glossentry">automatic</xref> smoke exhaust system complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/178_0.3.0.xml#_6d2c51ee-0d29-462a-a5c4-36126343e0bb" id="_7a9decec-c345-4393-a419-02434ee157f4" scope="local" type="specification">Specification 21</xref>.</li><li>If the building is single <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1483_25.0.0.xml#_53ff3ea1-55e7-4f2a-b2b3-ca445ff64c15" id="_b4dd00ef-b6b2-40b9-a161-81894738e11f" scope="local" type="abcb-glossentry">storey</xref>, <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_722475a0-e897-4466-a7bd-19fe70139dba" scope="local" type="abcb-glossentry">automatic</xref> <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1467_0.4.0.xml#_425cb075-105b-486b-834a-75d429b02edc" id="_fe27ffaa-5b7d-454a-874b-ca5c22d7c76d" scope="local" type="abcb-glossentry">smoke-and-heat vents</xref> complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/180_0.3.0.xml#_786dafbe-bc7c-47bb-9057-7afae7a7da08" id="_cc7fd949-422f-43f2-aa8e-165cbb746368" scope="local" type="specification">Specification 22</xref>.</li><li>A sprinkler system (other than a FPAA101D or FPAA101H system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_e409c92d-7e96-4c74-bf1a-5b8f890175dd" scope="local" type="specification">Specification 17</xref> with quick response sprinkler heads.</li></ol></li></ol></subclause></clause>