<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_421bf31c-4fef-4465-b700-f52a1b28135b" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S17C13</sptc><title id="_4b3faddb-0d01-45a1-9a0e-97df5825879d">Sprinkler systems in lift installations</title><archive-num>2019: Spec E1.5: 13</archive-num><subclause id="_d24d8a3d-5d87-4ced-95b2-081a03dd7b46" outputclass="subclause"><title id="_3c599757-2fcf-4b9f-8cc3-61f337fdd5fe">SubClause</title><num>1</num><p>Where sprinklers are installed in a space housing lift electrical and control equipment, including machine rooms, secondary floors and sheave rooms, sprinklers in these spaces must—</p><ol outputclass="alpha"><li id="_4e29d7d9-d318-4236-b44d-000a069f2337">have heads protected from accidental damage by way of a guard that will not impair the performance of the head; and</li><li id="_bb9383c9-b12e-43ce-a8a1-e055d92b1926">be capable of being isolated and drained, either separately or collectively, without isolating any other sprinklers within the building.</li></ol></subclause><subclause id="_82f1de34-33ff-4ce3-bdee-cf8df40518ff" outputclass="subclause"><title id="_b42757e3-2ea5-420d-943c-6ea645842a00">SubClause</title><num>2</num><p>Valves provided to control sprinklers referred to in (1) must be installed in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/605_5.2.0.xml#_bbea360b-0ed8-4164-8795-23bffee77340" id="_07f56cc3-7edb-4606-b810-227d059bff13" scope="local" type="subclause">S17C10(2)</xref>.</p></subclause></clause>