<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_c1caa03f-4f3d-4d4b-918a-4c51ee9ba4c7"><num>J6D5c</num><title id="_8fd04a78-267d-4c0f-8434-b0016b3a95c7">Fan regression coefficient b</title><table id="_c693b2c3-b831-4a67-bed8-141971ca1750" keycol="1"><tgroup cols="3"><colspec colname="001" colnum="1" colwidth="141.60*"/><colspec colname="002" colnum="2" colwidth="146.45*"/><colspec colname="003" colnum="3" colwidth="144.00*"/><thead><row><entry>Fan type</entry><entry>Fan motor input power &lt; 10 kW</entry><entry>Fan motor input power ≥ 10 kW</entry></row></thead><tbody><row><entry>Axial</entry><entry>6.33</entry><entry>1.88</entry></row><row><entry>Mixed flow</entry><entry>10.5</entry><entry>2.6</entry></row><row><entry>Centrifugal forward-curved</entry><entry>6.33</entry><entry>1.88</entry></row><row><entry>Centrifugal radial bladed</entry><entry>6.33</entry><entry>1.88</entry></row><row><entry>Centrifugal backward-curved</entry><entry>10.5</entry><entry>2.6</entry></row></tbody></tgroup></table></table-reference>