<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference xmlns:xt="urn:xpressauthor:trackchanges" graph="None" id="_c6671383-77d4-45d2-9708-c7180fd3256a"><num>J6D13</num><title id="_2836ed0d-1ccc-4c94-8ded-e3fa666917f7">Maximum fan motor power – Cooling towers, closed circuit coolers and evaporative condensers</title><table id="_13a85db5-fea8-492d-a9fd-7df2ae75786c" keycol="1"><tgroup cols="4"><colspec colname="001" colnum="1" colwidth="108.00*"/><colspec colname="002" colnum="2" colwidth="108.00*"/><colspec colname="003" colnum="3" colwidth="108.00*"/><colspec colname="004" colnum="4" colwidth="108.00*"/><thead><row><entry>Type</entry><entry>Cooling tower maximum fan motor input power (W/kW<xt:delText xt:action="start" xt:author="Jerome Samuel" xt:dateTime="2024-09-02T14:14:00" xt:id="786a3bdd-8deb-43d4-8637-0dfdd0fd9151"/><sub id="_bc6d490d-2325-4fe7-9107-511cd3169825">rej</sub><xt:delText xt:action="end" xt:id="786a3bdd-8deb-43d4-8637-0dfdd0fd9151"/>)</entry><entry>Closed circuit cooler maximum fan motor input power (W/kW<xt:delText xt:action="start" xt:author="Jerome Samuel" xt:dateTime="2024-09-02T14:14:00" xt:id="26980d07-a507-4873-a517-a057f324749f"/><sub id="_0d752f09-46e8-4bc9-a901-a1b74d9f5eb4">rej</sub><xt:delText xt:action="end" xt:id="26980d07-a507-4873-a517-a057f324749f"/>)</entry><entry>Evaporative condenser maximum fan motor input power (W/kW<xt:delText xt:action="start" xt:author="Jerome Samuel" xt:dateTime="2024-09-02T14:14:00" xt:id="303aa1d0-d1c9-4f4d-8b3c-5869b7eadc48"/><sub id="_aa0ebfe7-fd7e-4c6e-8b10-aa34121aab0a">rej</sub><xt:delText xt:action="end" xt:id="303aa1d0-d1c9-4f4d-8b3c-5869b7eadc48"/>)</entry></row></thead><tbody><row><entry>Induced draft</entry><entry>10.4</entry><entry>16.9</entry><entry>11.0</entry></row><row><entry>Forced draft</entry><entry>19.5</entry><entry>Note</entry><entry>11.0</entry></row></tbody></tgroup></table><desc-note id="_2517505f-5001-4db8-a3b7-112a0cb602ee"><p>A closed circuit, forced draft cooling tower must not be used.</p></desc-note></table-reference>