<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_744a4185-36b6-4379-bed9-1f8546bb5d74"><num>S7C3</num><title id="_0da2c33f-ff80-44db-9870-f1e09f5fc408">Critical radiant flux (CHF in kW/m<sup id="_8d4c9338-71f2-4722-947b-c10099b195e5">2</sup>) of floor linings and floor coverings</title><table id="_d440c4bc-cb72-4714-8a0c-4b30cedaf2b9" keycol="1"><tgroup cols="4"><colspec colname="001" colnum="1" colwidth="109.05*"/><colspec colname="002" colnum="2" colwidth="108.00*"/><colspec colname="003" colnum="3" colwidth="108.00*"/><colspec colname="004" colnum="4" colwidth="106.95*"/><thead><row><entry>Class of building</entry><entry>Building not fitted with a sprinkler system (other than a FPAA101D or FPAA101H system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_f931e127-6630-4622-9c88-cfcc89f82cf6" scope="local" type="specification">Specification 17</xref></entry><entry>Building fitted with a sprinkler system (other than a FPAA101D or FPAA101H system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_2f0ab24b-9682-49d8-9766-d50af6654a6d" scope="local" type="specification">Specification 17</xref></entry><entry>Fire-isolated <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1263_2.3.0.xml#_9712f630-8cf7-401b-b1cc-ae0be4485915" id="_472ae918-0917-433c-a449-a53701b414ea" scope="local" type="abcb-glossentry">exits</xref> and fire control rooms</entry></row></thead><tbody><row><entry>Class 2, 3, 5, 6, 7, 8 or 9b, excluding Class 3 accommodation for the aged and Class 9b as specified below</entry><entry>2.2 kW/m<sup id="_89cb517f-0f25-4a22-96e1-a27a2e5f6c01">2</sup></entry><entry>1.2 kW/m<sup id="_5dea6d0e-d15c-4dc6-a2a9-6c01d6651d30">2</sup></entry><entry>2.2 kW/m<sup id="_2509f503-d551-441d-b8ad-812c82f661be">2</sup></entry></row><row><entry>Class 3 accommodation for the aged</entry><entry>4.5 kW/m<sup id="_e379792a-fe2d-44d3-baae-87d1b068efa4">2</sup></entry><entry>2.2 kW/m<sup id="_4e6d7382-ff23-46a1-92b8-0f8f1e2659e8">2</sup></entry><entry>4.5 kW/m<sup id="_b97fbaeb-b786-459b-8964-0ff39ff191d2">2</sup></entry></row><row><entry>Class 9a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1393_4.0.0.xml#_63b56568-e9c9-425f-8456-a332503c9520" id="_09a6078d-4d89-4805-8f53-2e93b3aa9026" scope="local" type="abcb-glossentry">patient care areas</xref></entry><entry>4.5 kW/m<sup id="_2a59a235-a877-4849-9112-9e4e2fcba418">2</sup></entry><entry>2.2 kW/m<sup id="_a302c9c5-cc5e-4153-9efe-8aa9b7069cbf">2</sup></entry><entry>4.5 kW/m<sup id="_04d70c19-5b6f-4805-a5fd-89150532907f">2</sup>

</entry></row><row><entry>Class 9a areas other than <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1393_4.0.0.xml#_63b56568-e9c9-425f-8456-a332503c9520" id="_50b012a1-2ac1-4170-880c-2ded00d15a05" scope="local" type="abcb-glossentry">patient care areas</xref></entry><entry>2.2 kW/m<sup id="_1da55466-3f59-4d49-9b36-d4d56c2c8d21">2</sup></entry><entry>1.2 kW/m<sup id="_6e211c6e-78b4-441d-86a1-bc9552c27c22">2</sup></entry><entry>4.5 kW/m<sup id="_44605c9b-e150-4cc9-8d67-5a9899e967d2">2</sup></entry></row><row><entry>Class 9b auditorium or audience seating area used mainly for indoor swimming or ice skating</entry><entry>1.2 kW/m<sup id="_641b9673-cb56-48a0-943a-7648da9bb0a2">2</sup></entry><entry>1.2 kW/m<sup id="_79f05a13-8e0c-4516-8239-2aa60586b0b6">2</sup></entry><entry>2.2 kW/m<sup id="_78e77829-a57c-4acd-be39-ecc65540383c">2</sup></entry></row><row><entry>Class 9b auditorium or audience seating area used mainly for other sports or multi-purpose functions</entry><entry>2.2 kW/m<sup id="_c5bdbed2-b92b-493f-ab62-b56d0f7478d0">2</sup></entry><entry>1.2 kW/m<sup id="_54618353-32fa-40a6-86c0-52f5d8e58da0">2</sup></entry><entry>2.2 kW/m<sup id="_a3b5bcdc-a11b-4742-8aa0-7ce38798fe47">2</sup></entry></row><row><entry>Class 9c <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1437_4.0.0.xml#_071db02d-667d-447e-9f1e-8de8c46b9e0e" id="_594a1cea-fadf-42c8-99af-a9b88ecadef8" scope="local" type="abcb-glossentry">resident use area</xref></entry><entry>N/A</entry><entry>2.2 kW/m<sup id="_b5dc0cd5-18f9-4590-a3e0-a16b63ae19a0">2</sup></entry><entry>4.5 kW/m<sup id="_ba55d7cc-daa1-4794-b7bd-d49040f29eaf">2</sup></entry></row><row><entry>Class 9c areas other than <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1437_4.0.0.xml#_071db02d-667d-447e-9f1e-8de8c46b9e0e" id="_6ae32806-a7ee-4179-a060-65def5f6673a" scope="local" type="abcb-glossentry">resident use areas</xref></entry><entry>N/A</entry><entry>1.2 kW/m<sup id="_b0b9484f-db6d-407a-9e9e-00995464d0af">2</sup></entry><entry>4.5 kW/m<sup id="_7b763944-185c-4899-8130-8fe78078f93a">2</sup></entry></row></tbody></tgroup></table></table-reference>