<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_6d666f87-8697-4ce5-9e7b-28120972d59d" outputclass="ncc-clause" variation="NSW"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D55</sptc><title id="_9dc3e24f-f01d-41d9-8562-eaeeb4a05e7f">Lighting: lighting levels</title><archive-num>2019: NSW H101.20.2</archive-num><subclause id="_d8d8f5d9-ca35-4992-a4d5-a614d3cd1014" outputclass="subclause"><title id="_e45f3577-7713-40ae-b1e1-0c052da7443c">SubClause</title><num>1</num><p>Where the lamps utilised in the general lighting are of a type that will not relight immediately after the restoration of the primary electricity supply to those lamps—</p><ol outputclass="alpha"><li id="_f982af86-c5e6-4468-b520-3888e18d9176">a time delay or other suitable means must be provided to maintain the emergency lighting for a period not less than that necessary to allow the general lighting lamps to restrike; or</li><li id="_0bcc8ff8-1b8e-47c8-935d-757b8adcc15f">lamps of a type that will provide immediate lighting must be installed and—<ol><li id="_55b766b8-8da0-431a-b892-dca008771b06">arranged in such a manner as to ensure visual conditions not inferior to those <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_68e3f2ed-9098-4bb1-8ecf-4960a57b8828" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">required</xref> to be provided by the emergency lighting; and</li><li>capable of being switched in common with the general lighting and of being controlled also by the override switch <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_35aa7f38-22f4-4a79-b2f5-736c0ba784ba" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">required</xref> by <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6763_0.4.0.xml#_c10ed94d-f68b-4476-b8e5-4e290790b2bc" id="_1bd598c2-f861-4daa-b2ee-4b2f6af6a96d" referencetype="Text" scope="local" synctargettext="false" type="subclause">NSW I4D54(2)</xref>.</li></ol></li></ol></subclause></clause>