<?xml version="1.0" encoding="UTF-8" standalone="no"?><table-reference graph="None" id="_51e43184-1a58-4f7b-ab3c-919040fc8e40"><num>S10C3</num><title id="_06955107-06df-4123-b5f6-4e9277fc7665">Interface temperature and minimum fire protective grade plasterboard thickness</title><table id="_206c6d59-ab25-49fe-a642-ac93034b679b" keycol="1"><tgroup cols="3"><colspec colname="001" colnum="1" colwidth="144.00*"/><colspec colname="002" colnum="2" colwidth="144.00*"/><colspec colname="003" colnum="3" colwidth="144.00*"/><thead><row><entry>Application</entry><entry>Time – without timber interface exceeding 300°C (mins)</entry><entry>Minimum thickness of fire-grade plasterboard (mm)</entry></row></thead><tbody><row><entry>Inside a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1285_2.1.0.xml#_c71e675e-d6e1-4612-8e59-381a56e224a8" id="_cc1a2a88-caf6-41aa-94da-7b425fb33dd4" scope="local" type="abcb-glossentry">fire-isolated stairway</xref> or lift shaft</entry><entry>20</entry><entry>13</entry></row><row><entry><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_ba190d51-7de0-4db6-923c-482948bd22b9" scope="local" type="abcb-glossentry">External walls</xref> within 1 m of an allotment boundary or 2 m of a building on the same allotment</entry><entry>45</entry><entry>2 x 13</entry></row><row><entry>All other applications</entry><entry>30</entry><entry>16</entry></row></tbody></tgroup></table></table-reference>