<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_19451430-4c99-4197-94f8-4205b0ed636a" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 4"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/><facet climate="Climate zone 1"/><facet climate="Climate zone 2"/><facet climate="Climate zone 3"/><facet climate="Climate zone 4"/><facet climate="Climate zone 5"/><facet climate="Climate zone 6"/><facet climate="Climate zone 7"/></meta><sptc>G4D7</sptc><title id="_a365a31f-da02-4c06-8fa5-098977814f2b">Fire-fighting services and equipment</title><archive-num>2019: G4.8</archive-num><subclause id="_2d30cbe7-1f2e-4d9c-8c48-c2d940ff0d54" outputclass="subclause"><title id="_298cc3fe-a602-4b94-a178-838ee6979054">SubClause</title><num>1</num><p>Every Class 2, 3, 5, 6, 7, 8 or 9 building must have—</p><ol outputclass="alpha"><li id="_b940e5e1-d834-4fc7-81e4-fca0b71442a0">a manually operated fire alarm system with call-points complying with AS 1670.1; and</li><li id="_6c66475e-2840-49c3-a3e8-a4d0c2dd9397">fire hydrants installed in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2608_1.15.0.xml#_7d9ae74c-2634-4d13-8e63-fb28728dff6d" id="_aea0b2f3-7a93-4d1e-b7d5-38f5d3b83610" scope="local" type="subclause">E1D2(2)</xref>; and</li><li id="_3637b0d9-66cd-4dbc-a99c-da411b7b72c8">fire hose reels installed in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2612_1.15.0.xml#_21ac0619-468a-4a21-ae8a-eda0480d2bde" id="_3f1348e6-3b55-4d0e-97ed-433eee2dd8ba" scope="local" type="subclause">E1D3(2)</xref> to <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2612_1.15.0.xml#_e21233eb-413c-4b1a-aa55-cc612f2f4b54" id="_41712a3d-6777-43f3-8987-23adfdb8c0fb" scope="local" type="subclause">(7)</xref>, except that in a Class 2 or 3 building—<ol><li>for the purpose of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2612_1.15.0.xml#_21ac0619-468a-4a21-ae8a-eda0480d2bde" id="_1cb6da14-c099-43cb-93d7-b29e49b21443" scope="local" type="subclause">E1D3(2)</xref>, a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_b15423f6-902e-4c5e-a896-0a279391fa71" scope="local" type="abcb-glossentry">sole-occupancy unit</xref> is considered to be a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1277_2.0.0.xml#_524b0326-5823-4ddc-9eb3-adab587568e8" id="_7f8d50a8-4964-4e31-afe2-5337aaa76324" scope="local" type="abcb-glossentry">fire compartment</xref>; and</li><li>for the purpose of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2612_1.15.0.xml#_f834c284-1651-45df-b717-3e02b5d238f1" id="_16752ba6-1d9a-4712-a3a1-8116b6a0868e" scope="local" type="subclause">E1D3(3)(b)</xref>, a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_2bf85c12-ef33-4f48-82a9-7dc334e16cf1" scope="local" type="abcb-glossentry">sole-occupancy unit</xref> may be served by a single fire hose reel located at the level of egress from that <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1473_0.4.0.xml#_d2c89488-8a36-464b-94f6-a91d0f5a6c9c" id="_0be159e2-ee20-43e7-8e07-cbea47957eef" scope="local" type="abcb-glossentry">sole-occupancy unit</xref>; and</li><li>for the purpose of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2612_1.15.0.xml#_46faa3de-ed3a-473e-a235-fd07706adb17" id="_06b0f344-3602-4adf-9e01-afb43dba3554" scope="local" type="subclause">E1D3(6)</xref>, a fire hose may pass through a doorway in bounding construction referred to in <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1417_1.3.0.xml#_7bd85bd6-cbfa-418f-ba00-0d75ff33b937" id="_b8da1ee4-bb75-46f4-9ea6-f40040fcf52e" scope="local" type="clause">C4D12</xref>.</li></ol></li></ol></subclause><subclause id="_38f565b9-599c-4cbf-b856-1120bec30a3a" outputclass="subclause"><title id="_016fadb7-c63d-4fad-b344-a0bc6d7a003c">SubClause</title><num>2</num><p>The requirements of (1)(c) do not apply to a Class 8 <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1255_0.4.0.xml#_7a37df1f-0b8b-4b03-94ca-69ea423a363f" id="_5256c2da-b190-4cbc-9305-98633e353507" scope="local" type="abcb-glossentry">electricity network substation</xref>.</p></subclause></clause>