<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_53f77669-5748-4951-8fb5-d537eefec84a" outputclass="ncc-clause" variation="TAS"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D18</sptc><title id="_8ac8e9c9-8c23-4db5-9391-dae83f66ae3c">Refrigerated and cooling chambers</title><archive-num>2019: TAS H102.17</archive-num><subclause id="_3aafe28d-923c-46fe-ac81-b49cebe05fec" outputclass="subclause"><title id="_2b3dcd4e-b393-453e-a986-c010e06c0b7c">SubClause</title><num>1</num><p>The construction of a refrigerated chamber or cooling chamber installed in premises for storage of food complying with the requirements for that premises, satisfies <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6838_0.3.0.xml#_757ba051-8c39-403a-b751-145a702509e7" id="_740a82be-7117-4f61-abfa-a39c7e87f55f" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">TAS I4P13</xref> where they have—</p><ol outputclass="alpha"><li id="_3f859124-fe2e-4eb7-a414-c515d66ef013">internal and external panels adhered directly to the insulated core material to form an integral wall section with tight fitting edges resistant to penetration by liquids; and</li><li id="_a9d04e1e-8b96-48d6-ac4d-9c20f7b842be">every joint caulked with a water-resistant, flexible sealer and finished in such a manner as to prevent migration of liquids into the core; and</li><li id="_a8cc3299-d59e-4703-b842-aa1ff6e846d3">every intersection of walls with floors and walls with walls coved with a radius not less than 25 mm; and</li><li id="_143ccfeb-5aff-4096-97b9-1c3da06f30f7">exposed slot-head screws or open-headed pop rivets filled with sealer; and</li><li id="_a30018ed-c16f-45c5-a2f5-3c7794c3b6e6">service pipes and conduits concealed in floors, walls or ceilings, if practicable, or fixed on brackets to provide clearances of not less than 25 mm between the pipe and a wall and 100 mm between the pipe and a floor; and</li><li id="_08465cb8-c179-404e-b53a-ab42af1ef27f">fittings not fixed over exposed pipes nor in a position to make difficult the cleaning of the pipe and surrounding area; and</li><li id="_b6623c09-a1db-40c4-9d00-83c55e85016a">rat proof construction, and any inaccessible spaces between the low temperature room and surrounding walls, ceilings and fixtures proof against rats an vermin; and</li><li id="_42e51090-7f34-4746-bfd2-b04862a32e4f">floor graded, as shown in <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6857_0.2.0.xml#_58181382-8d5c-4009-9227-1dff062ed65c" id="_48d6a686-d60b-4be9-8da4-af13ac5ecfd3" referencetype="Text" scope="local" synctargettext="false" type="table-reference">Table TAS I4D18a</xref>, to drains located outside the chamber as near as practicable to the door opening; and</li><li id="_31763f7c-98b9-437e-919b-63c94bf85776">drainage from cooling units within the chamber constructed in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6858_0.2.0.xml#_a53bd401-41af-47d7-9913-87c1696853ab" id="_148635bf-189c-4a15-949e-4c19fc0fac70" referencetype="Text" scope="local" synctargettext="false" type="table-reference">Table TAS I4D18b</xref>, draining to a trapped outlet located outside the chamber.</li></ol></subclause><table-reference conref="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6857_0.2.0.xml" graph="None" id="_58181382-8d5c-4009-9227-1dff062ed65c" variation="TAS"><num/><title id="_8ba6131c-9b3c-4b8e-a747-2a92d619cea2"/></table-reference><table-reference conref="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6858_0.2.0.xml" graph="None" id="_a53bd401-41af-47d7-9913-87c1696853ab" variation="TAS"><num/><title id="_066889e4-c595-4689-84a1-9f1476974279"/></table-reference></clause>