<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause"?><clause id="_16de0f92-21a7-4f03-bd30-c684b3bd30de" outputclass="ncc-clause" variation="VIC"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D6</sptc><title id="_58ed8012-c2aa-4ac8-ac13-b6ce183d9830">Electronic communication system</title><archive-num>2019: VIC H101.6</archive-num><subclause id="_dae0beca-14ad-4588-9619-ef66d318ee50" outputclass="subclause"><title id="_cee71122-d9ce-4c40-9077-61afed6f8102">SubClause</title><num>1</num><p>A communication system must—</p><ol outputclass="alpha"><li id="_cc82063a-4a0f-4989-8b8d-15256842850f">contain a back-up power supply; and</li><li id="_e92612b6-ac52-496d-9cd0-0fc2dadaff9b">have a control that enables the call to be cancelled manually at the point of origin only; and</li><li id="_ce701555-47ce-449e-aeb8-cab73060e669">incorporate a device at the point of origin that indicates the system has operated; and</li><li id="_207f731a-c38b-4d67-ace9-906993343fe9">incorporate an indication panel in the manager’s office or staff area that clearly indicates the point of origin of a call; and</li><li id="_b6764d61-8a48-4ec3-9b2b-b4b441133b98">have an audible tone that has a continuous signal until deactivated at the point of origin; and</li><li id="_4cc0dba0-bc41-4cdb-a5b7-5fca8bbfc6de">be operational at all times; and</li><li id="_43b79098-3328-4b9c-b89a-ef3a87361e9b">have two call points in each ensuite or combined shower/water closet with one call point located in the shower recess and the other on the wall beside the closet pan ahead of the bowl rim; and</li><li id="_c7debace-d3d6-43ef-979b-bbcbbe432358">have call points (other than those mentioned in (g)) which are located—<ol><li id="_b7c0ef0f-aaed-4f18-bbf8-b1f453877331">within the reach of a resident whilst in bed; and</li><li>in all common <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1326_0.4.0.xml#_b8eec66f-9c05-425d-8474-e6a2dfc2c0f4" id="_26d63e42-9c89-4e65-8d3f-278b9077520a" inv:access="external" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">habitable rooms</xref>; and</li><li>in all bathrooms, <xref xmlns:inv="urn:xpressauthor:xpressdocument" format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1445_0.13.0.xml#_b30a308f-eb9f-4549-a6c1-19d5f32a5272" id="_01a648d4-5f19-4a80-a035-67992fae51a8" inv:access="external" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">sanitary compartments</xref> and shower rooms where the call point must be of waterproof construction and within the reach of any fallen resident.</li></ol></li></ol></subclause></clause>