<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_4c25e47b-e93b-49be-9981-a9003b120a1e" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S31C2</sptc><title id="_78c2ed49-55f2-4fe2-946f-86543e505e38">General requirement — automatic fire sprinkler system</title><archive-num>2019: Spec G3.8: 2.1</archive-num><subclause id="_9a9d944b-cbd9-4a67-9418-c2b7b911b36f" outputclass="subclause"><title id="_39e08535-b01c-48a6-bb4a-8483129a9a83">SubClause</title><num>1</num><p>A sprinkler system (other than a FPAA101D or FPAA101H system) complying with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/167_0.8.0.xml#_481171d2-3952-490d-b64d-c3d3f5d7825a" id="_480ea074-ea14-4885-becb-ce5fe0059290" scope="local" type="specification">Specification 17</xref> must be installed in every building containing an <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1197_1.0.0.xml#_d0042ee6-21cd-4d8c-8873-d8bfb694ceff" id="_af52f425-e2c8-4f5e-8278-5b387298a02c" scope="local" type="abcb-glossentry">atrium</xref>, except where varied or superseded by this Specification.</p></subclause></clause>