<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause id="_3e9b3dbe-49cc-4d48-b6b4-e15bd3e06912" outputclass="ncc-clause" variation="NSW"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>I4D59</sptc><title id="_11f9d19f-6c1a-4ae3-9d4d-1b2ff96e5c0d">Automatic smoke-and-heat vents for stages</title><archive-num>2019: NSW H101.22</archive-num><subclause id="_8f1b3b02-8757-4b03-8b33-a01cf3ae6c8a" outputclass="subclause"><title id="_203c8508-a384-4c2d-85cc-14135682b14d">SubClause</title><num>1</num><p>An <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_0f8cb0d4-989a-4cc0-bcb8-580b1ee3e0e0" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">automatic</xref> <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1467_0.4.0.xml#_425cb075-105b-486b-834a-75d429b02edc" id="_b073bd85-28c6-48bd-a6fe-45d210d71a21" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">smoke-and-heat vent</xref> system <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_6a660b0e-fddc-442b-9d57-fed76341956c" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">required</xref> by <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/4259_2.3.0.xml#_8f7e230e-b4d4-4b3b-a325-123311821d12" id="_b2eeff28-7eb2-4970-ab34-ecf6d9cadae4" referencetype="Text" scope="local" synctargettext="false" type="ncc-clause">NSW E2D16(c)</xref> for <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_14cc3e39-74fe-4f10-aae6-7c620a38b23c" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stages</xref> and <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1207_1.0.0.xml#_a664353a-ef5b-4cd2-b68b-f2db1db81dce" id="_fc1e13bd-fd40-4560-a244-2009a674864b" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">backstages</xref> must—</p><ol outputclass="alpha"><li id="_f2eece76-9993-4832-ba2d-0772f00aeb70">be capable of <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_7460f201-185f-43f8-94a6-d87e2ae7c61e" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">automatic</xref> operation by the inclusion of a heat sensing device designed to activate the system at a temperature of not more than 71°C; and</li><li id="_ddd6c4df-c0de-4b7d-a3df-34c89fb0fc15">be capable of being released manually from positions at either side of the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_6fe6cb0b-3588-40ee-9652-d016d98aecf4" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stage</xref> and of being fully activated from either position; and</li><li id="_b0b62313-7489-46ba-a254-f827701b4345">have a notice, prominently displayed at each position referred to in (b), clearly indicating the method of activation; and</li><li id="_de268adf-474e-45d7-8b88-2fa5300f040c">have an openable area of not less than 10 percent of the total area of the <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1478_0.4.0.xml#_02701ef9-5783-4b2b-af0e-4a764b0375ed" id="_9aae4485-ee8e-4082-b1bc-5eb00942cd09" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">stage</xref>.</li></ol></subclause></clause>