<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_6f2a86e6-c70a-408e-8ef3-5eb36d79a194" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 10a"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S20C8</sptc><title id="_0880844f-f60b-40b0-988e-c687d5c8be70">System monitoring</title><archive-num>2019: Spec E2.2a: 8</archive-num><clause-variation href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6035_0.4.0.xml" variation="NSW" variation-type="REPLACE">NSW REPLACE Clause</clause-variation><clause-variation href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/6036_0.5.0.xml" variation="VIC" variation-type="REPLACE">VIC REPLACE Clause</clause-variation><subclause id="_8fba242d-ac97-4ea4-84e9-dda9c2969402" outputclass="subclause"><title id="_699dfd20-2772-4a46-b77e-0b9ef7b32de2">SubClause</title><num>1</num><p>The following installations must be connected to a fire alarm monitoring system connected to a fire station or fire station dispatch centre in accordance with AS 1670.3:</p><ol outputclass="alpha"><li id="_3607f904-ab09-4419-9e28-2f568d24928c">A smoke detection system in a Class 3 building provided in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_4fb9883e-9f7d-458e-8f3c-86c68910ed3e" id="_760e7580-249d-4e63-8859-658e77895389" scope="local" type="clause">S20C2(b)(i)</xref> or <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/666_6.2.0.xml#_4fb9883e-9f7d-458e-8f3c-86c68910ed3e" id="_b2fb78bf-504a-4a9c-911f-4ddb0978e738" scope="local" type="clause">S20C2(b)(ii)</xref>.</li><li id="_a8635c6f-8646-41e3-97db-40cab86ade8b">A smoke detection system in a Class 9a <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1333_0.4.0.xml#_1f5fbee8-584a-4244-9286-ebf9d8ebb04a" id="_73c5eced-1a05-49bc-829d-7f882941be3a" scope="local" type="abcb-glossentry">health-care building</xref>, if the building accommodates more than 20 patients.</li><li id="_34b5922d-8212-4924-bfa9-d70d59f9479a">A smoke detection system in a Class 9c building.</li><li id="_d36cf1ad-b392-4414-9ebf-24a142a79649">Smoke detection in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/672_7.5.0.xml#_38696b94-36c5-42a0-a851-78ecd6b31308" id="_cebae571-9570-4a38-8215-539b56289aec" scope="local" type="clause">S20C6</xref> provided to activate—<ol><li>a smoke exhaust system in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/178_0.3.0.xml#_6d2c51ee-0d29-462a-a5c4-36126343e0bb" id="_08f61199-0ddc-4f13-8ce5-2e07c337f94e" scope="local" type="specification">Specification 21</xref>; or</li><li><xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1467_0.4.0.xml#_425cb075-105b-486b-834a-75d429b02edc" id="_2039d8aa-34fd-40a6-850d-c4b1c3971f1e" scope="local" type="abcb-glossentry">smoke-and-heat vents</xref> in accordance with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/180_0.3.0.xml#_786dafbe-bc7c-47bb-9057-7afae7a7da08" id="_e30a45f9-1f4c-4348-844f-2e39c7d4028d" scope="local" type="specification">Specification 22</xref>.</li></ol></li><li id="_eac87212-8887-4b0c-8b38-462d89fd85e2">An <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1199_0.7.0.xml#_ac370c9b-7389-4daa-ac5b-338e11dc43e7" id="_ee1f4abb-ce71-42d6-a200-923b9ab23c54" scope="local" type="abcb-glossentry">automatic</xref> fire detection and alarm system <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_af6fde9f-147d-4782-8b85-42044e80fd42" id="_fcbffa9c-160a-4c24-866a-c59c8879c3ed" scope="local" type="abcb-glossentry">required</xref> by <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/2703_1.9.0.xml#_b7abbb05-33f2-434d-a550-8f0b3d2c865e" id="_4b5f65d5-9652-43e2-b159-326cf80c85d6" scope="local" type="clause">E2D10</xref> for large isolated buildings subject to <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1152_1.7.0.xml#_6ed8026f-71b8-4618-a419-79b7053b0c98" id="_987fd9ae-df58-45c3-904a-12faf488b262" scope="local" type="clause">C3D4</xref>.</li></ol></subclause></clause>