<?xml version="1.0" encoding="UTF-8" standalone="no"?><?Xpress productLine="ncc-clause" ?><clause xmlns:xt="urn:xpressauthor:trackchanges" id="_bc4f6078-9307-4a9c-b4e1-688803408626" outputclass="ncc-clause"><meta><facet building="Class 1a"/><facet building="Class 1b"/><facet building="Class 2"/><facet building="Class 3"/><facet building="Class 4"/><facet building="Class 5"/><facet building="Class 6"/><facet building="Class 7a"/><facet building="Class 7b"/><facet building="Class 8"/><facet building="Class 10b"/><facet building="Class 10c"/></meta><sptc>S43C4</sptc><title id="_847a8bc9-1962-4113-8c33-3be8d7a445e4">Separation from allotment boundaries and carparking areas</title><archive-num>New for 2022</archive-num><subclause id="_6724b1a7-9c7a-4aaf-bc3e-e7fe8cf9567b" outputclass="subclause"><title id="_022a6a0b-6733-423f-b3a3-5cdceff7b75e">SubClause</title><num>1</num><p>The building must be located not less than 10 m from any allotment boundary or open carparking area/spots.</p></subclause><subclause id="_846befe9-dfdc-44f8-8e97-599c6cfa76e8" outputclass="subclause"><title id="_8993af7c-1ffd-447e-8204-9dc72a4e46e9">SubClause</title><num>2</num><p>The separation distance <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1432_4.0.0.xml#_a5b45a91-1ac3-44a8-8644-acfc09c225a9" id="_1fe3b838-e89a-4c5a-9563-32dc380b9350" referencetype="Text" scope="local" synctargettext="false" type="glossterm">required</xref> by (1) need not be complied with if the building is constructed—</p><ol outputclass="alpha"><li id="_014c5a5c-098d-4d1b-9959-675e55652b52">with <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_2deff2f6-c8e5-4fc0-b558-df4339570c77" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> that have an FRL of not less than 60/60/60 when tested from the outside, including any openings protected in accordance with AS 3959 for BAL—19 or greater; or</li><li id="_3b912e76-9a68-4bfc-ab54-c912b60d5f84">for <xref format="dita" href="/tmp/QppServer/Publishing/5e2c1f63-e589-4ce1-95e8-5c3e286a7aff/1267_2.3.0.xml#_d87c7cc0-d0b0-40ab-9a5b-d070ed6e115e" id="_f9b15d05-54e7-4534-ada5-8ddf48c5fae6" referencetype="Text" scope="local" synctargettext="false" type="abcb-glossentry">external walls</xref> and roof, using a material or system that satisfies the test criteria of AS 1530.8.1 for a radiant heat flux of 10 kW/m² or greater.</li></ol></subclause></clause>